Main rangePowerLogic device short nameION8800A product or component typeEnergy and power quality meter Complementary power quality analysisconforming to IEC 61000-4-15 flicker magnitude harmonic up to the 50th conforming to IEEE 519: 1992 harmonic control conforming to IEEE 1159: 1995 power quality monitoring symmetrical component transient detection (20 µs) voltage sag and swell detection programmablity (logic and math functions) up to the 63rd harmonic conforming to IEC 61000-4-30: class A power quality measurement conforming to EN 50160 compliance report device applicationCo-generation and IPP monitoringInstrument transformer correctionContract optimisationLoad curtailmentPower monitoringEnergy pulsing and totalisationDemand and power factor controlEquipment monitoring and controlTariff metering type of measurementCurrentVoltageFrequencyApparent power totalPower factor totalApparent power per phasePower factor per phaseActive power totalActive power per phaseReactive power totalReactive power per phase supply voltage85...240 V AC 47...63 Hz110...270 V DC network frequency50 Hz [In] rated current5 A type of network3P + N3P1P + N power consumption in VA19 VA maximum power consumption in VA32 VA display typeFSTN transflective LCD sampling rate1024 samples/cycle measurement current0…5 A input typecurrent 0.001...10 A (impedance 0.01 Ohm) measurement voltage57…288 V AC phase to neutral99…500 V AC phase to phase frequency measurement range47…63 Hz number of inputs3 digital 20...56 V AC/DC measurement accuracyCurrent 0.1 %Voltage 0.1 %Power 0.2 %Power factor 0.1 %Frequency 0.005 HzEnergy 0.2 % accuracy classClass 0.2S active energy conforming to IEC 62053-22Class 0.2S reactive energy conforming to IEC 62053-23 number of outputs1 alarm output4 form C solid state output2 IEC 1107 pulse communication port protocolDLMSIONTCP/IP at 10/100 Mbit/sDNP3Modbus RTU, master/slave at <= 19200 baudsModbus RTU, master/slave at 300...57600 baudsModbus RTU, master/slave at 300...115200 baudsModbus TCP, master/slave at 10/100 Mbit/sIEC 1107 at <= 19200 bauds communication port supportScrew terminal block: RS485RJ45: EthernetInfraredDB9: RS485/RS232 time synchronisation protocolIRIG-B data recordingTransient logsData logsTime stampingGPS synchronisationAlarmsWaveform logsMin/max of instantaneous valuesHistorical logs transmission rate<= 19200 bauds10/100 Mbit/s300...57600 bauds300...115200 bauds memory capacity10 MB web servicesWeb server tamperproof of settingsProtected by access code compatibility codeION8800A Environment electromagnetic compatibilityConducted RF disturbances conforming to IEC 61000-4-6Immunity to impulse waves conforming to IEC 61000-4-12Electrical fast transient/burst immunity test conforming to IEC 61000-4-4Electrostatic discharge conforming to IEC 61000-4-2Susceptibility to electromagnetic fields conforming to IEC 61000-4-31.2/50 µs shock waves immunity test conforming to IEC 61000-4-5Conducted and radiated emissionsB conforming to CISPR 22 mounting modeRack-mounted enclosure type19" rack type of installationIndoor installation overvoltage categoryIII IP degree of protectionIP51 conforming to IEC 60529 relative humidity5…95 % pollution degree2 ambient air temperature for operation-10…45 °C ambient air temperature for storage-25…70 °C operating altitude0...2000 m product certificationsEGRESKOMGOSTNMI standardsIEC 62052-11IEC 60950 width202.1 mm depth261.51 mm height132.2 mm net weight6 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Documents & DownloadsLanguage
User guideSizeAdd to My DocumentsION Reference -EN (Version 10)DLMS/COSEM and ION technology (Version 04)IEC 61000-4-30 compliance and ION meters -EN (Version 12)CertificateSizeAdd to My DocumentsCatalogue pageSizeAdd to My DocumentsFirmware - ReleasedSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.