Main rangeLinergy product nameLinergy BS product or component typeBusbar support Complementary cubicle-device connectionLinergy BS lateral busbar installation descriptionFloor-standing duct - width 300 mmWall-mounted duct - width 300 mm permissible current160 A - busbar cross section: 15 x 5 mm250 A - busbar cross section: 20 x 5 mm400 A - busbar cross section: 32 x 5 mm630 A - busbar cross section: 32 x 8 mm [Icw] rated short-time withstand current10 kA (1 s) at 160 A for 450 mm between support centres20 kA (1 s) at 400 A for 300 mm between support centres13 kA (1 s) at 250 A for 450 mm between support centres15 kA (1 s) at 400 A for 450 mm between support centres15 kA (1 s) at 630 A for 450 mm between support centres20 kA (1 s) at 630 A for 300 mm between support centres25 kA (0.6 s) at 400 A for 300 mm between support centres25 kA (1 s) at 630 A for 300 mm between support centres quantity per setSet of 1 net weight0.2 kg Environment standardsIEC 61439-1IEC 61439-2 product certificationsASEFA Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 84.4 MBDate 10/18/19DescriptionThis catalogue includes Spacial S3D rangesprp.document.label.format pdfSize 82.2 MBDate 10/10/19DescriptionDistribution and connection systems catalogueCADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages17
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.