Main range of productNG160 product or component typeCircuit breaker device short nameNG160N circuit breaker nameNG160N device applicationDistribution poles description4P protected poles description4t network typeAC network frequency50/60 Hz [In] rated current32 A at 40 °C breaking capacity codeN breaking capacity10 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-216 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-225 kA Icu at 380...415 V AC 50/60 Hz conforming to IEC 60947-240 kA Icu at 220...240 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity30 kA at 220/240 V AC 50/60 Hz7.5 kA at 500 V AC 50/60 Hz12 kA at 440 V AC 50/60 Hz18.75 kA at 380/415 V AC 50/60 Hz suitability for isolationYes trip unit nameTM-D trip unit technologyThermal-magnetic trip unit rating32 A protection typeOverload protection (thermal)Short-circuit protection (magnetic) Complementary control typeToggle mounting modeClipped mounting support35 mm symmetrical DIN rail upside connectionFront downside connectionFront connections - terminalsTunnel type terminals mechanical durability10000 cycles electrical durability5000 cycles 440 V local signallingON/OFF indication magnetic tripping current600 A long time pick-up adjustment type IrFixed earth-leakage protectionSeparate block height120 mm width120 mm depth82.5 mm product compatibilitySingle terminal Environment standardsIEC 60947-3 Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsSize zipSize 3.8 MBDate 11/14/07Size zipSize 3.8 MBDate 11/14/07Size zipSize 3.8 MBDate 11/14/07EU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.