Main rangeCompact product nameCompact NS range of productNS630b...1600 device short nameCompact NS800H product or component typeCircuit breaker device applicationDistribution poles description3P protected poles description3d (In) rated current up to 65 °C800 A at 50 °C [Ue] rated operational voltage690 V AC 50/60 Hz network typeAC network frequency50/60 Hz suitability for isolationYes conforming to EN/IEC 60947-2 utilisation categoryCategory B [Icu] rated ultimate short-circuit breaking capacity42 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-265 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-270 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-285 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 500/525 V AC 50/60 Hz conforming to IEC 60947-2 Performance levelH 70 kA 415 V AC trip unit nameMicrologic 2.0 E trip unit technologyElectronic trip unit protection functionsLI control typeRotary handleToggle Circuit breaker mounting modeFixed Complementary [Ui] rated insulation voltage800 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 [Ics] rated service short-circuit breaking capacity30 kA at 660/690 V AC 50/60 Hz conforming to IEC 60947-240 kA at 500/525 V AC 50/60 Hz conforming to IEC 60947-250 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-250 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-250 kA at 440 V AC 50/60 Hz conforming to IEC 60947-2 [Icw] rated short-time withstand current19.2 kA 1 s conforming to IEC 60947-2 mechanical durability10000 cycles electrical durability2000 cycles at 690 V In4000 cycles at 690 V In/25000 cycles at 440 V In6000 cycles at 440 V In/2 power losses15 W mounting supportBackplate upside connectionFront downside connectionFront connection pitch70 mm protection typeL : for overload protection (long time)I : for instantaneous short-circuit protection trip unit rating800 A at 50 °C Long-time pick-up adjustment type Ir (thermal protection)Adjustable 9 settings [Ir] long-time protection pick-up adjustment range0.4...1 x In Long-time protection delay adjustment type trAdjustable 9 settings [tr] long-time protection delay adjustment range12.5…600 s at 1.5 x Ir0.5…24 s at 6 x Ir0.7…16.6 s at 7.2 x Ir thermal memory20 mn Instantaneous protection pick-up adjustment type IiAdjustable [Ii] instantaneous protection pick-up adjustment range1.5...10 x Ir zone selective interlocking ZSIWith auxiliary contact composition1 NO/NC local signalling4 LEDs (red)fault indication: 1 LED (yellow)overload: display typeLCD display type of measurementEnergy meter Width (W)210 mm Height (H)327 mm Depth (D)147 mm net weight14 kg Environment standardsEN/IEC 60947-2 product certificationsASTAASEFA pollution degree3 conforming to IEC 60947 IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to EN 50102 ambient air temperature for operation-25…70 °C ambient air temperature for storage-40…85 °C relative humidity0…95 % operating altitude0...2000 m without derating2000 m...5000 m with derating Packing Units Package 1 Weight11.890 kg Package 1 Height37.000 cm Package 1 width39.500 cm Package 1 Length23.000 cm Offer Sustainability Sustainable offer statusGreen Premium product REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeDateAdd to My DocumentsCADFormatSizeDateAdd to My DocumentsInstruction sheetFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsEU RoHS DeclarationFormatSizeDateAdd to My DocumentsMarine certificateFormatSizeDateAdd to My Documents
- All Languages10
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.