Main rangeCompact range of productNS630b...1600 product or component typeCircuit breaker device short nameCompact NS800N device applicationDistribution poles description4P protected poles description4t neutral positionLeft network typeAC breaking capacity codeN suitability for isolationYes conforming to IEC 60947-2 utilisation categoryCategory B trip unit nameMicrologic 5.0 E trip unit technologyElectronic trip unit rating800 A at 50 °C Complementary network frequency50/60 Hz control typeRotary handleToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront (In) rated current up to 65 °C800 A at 50 °C [Ui] rated insulation voltage800 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-2 circuit breaker CT rating800 A breaking capacity30 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-285 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-240 kA Icu at 500/525 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity30 kA at 660/690 V AC 50/60 Hz conforming to IEC 60947-240 kA at 500/525 V AC 50/60 Hz conforming to IEC 60947-250 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-250 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-250 kA at 440 V AC 50/60 Hz conforming to IEC 60947-2 auxiliary contact composition1 NO/NC mechanical durability10000 cycles electrical durability2000 cycles 690 V AC 50/60 Hz In conforming to IEC 60947-24000 cycles 690 V AC 50/60 Hz In/2 conforming to IEC 60947-25000 cycles 440 V AC 50/60 Hz In conforming to IEC 60947-26000 cycles 440 V AC 50/60 Hz In/2 conforming to IEC 60947-2 local signallingPositive contact indication [Icw] rated short-time withstand current19.2 kA neutral protection settingIr trip unit protection functionsLSI protection typeShort time short-circuit protectionOverload protection (long time)Instantaneous short-circuit protection long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.4...1 x In long time delay adjustment typeAdjustable 9 settings [tr] long-time delay adjustment range0.7…16.6 s 7.2 x Ir12.5…600 s 1.5 x Ir0.5…24 s 6 x Ir thermal memory20 mn short-time pick-up adjustment type IsdAdjustable 9 settings [Isd] short-time pick-up adjustment range1.5...10 x Ir short-time delay adjustment typeAdjustable [tsd] short-time delay adjustment range0.1…0.4 s I²t=on0…0.4 s I²t=off [tsd] short-time delay adjustment range0.02…0.5 s instantaneous pick-up adjustment type IiAdjustable instantaneous pick-up adjustment rangeOff2...15 x In integrated instantaneous protection40 kA zone selective interlocking ZSIWith display typeLCD display type of measurementEnergy meter height327 mm width280 mm depth147 mm Environment standardsIEC 60947-2 product certificationsASEFAASTA power losses15 W IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to EN 50102 pollution degree3 conforming to IEC 60947 ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsMarine certificateFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.