Main rangeMasterpact product nameMicrologic product or component typeControl unit device applicationDistribution poles description3P4P protected poles description4t3t3t + N/2 network typeAC network frequency50/60 Hz trip unit nameMicrologic 5.0 A trip unit technologyElectronic trip unit protection functionsSelective protection protection typeShort time short-circuit protectionInstantaneous short-circuit protectionOverload protection (long time) trip unit rating3200 A at 50 °C Complementary mounting modeFixed long time pick-up adjustment type IrAdjustable 9 settings long time pick-up adjustment range0.4...1 x In long time delay adjustment typeAdjustable 9 settings [tr] long-time delay adjustment range0.7…16.6 s 7.2 x Ir0.7…24 s 6 x Ir12.5…600 s 1.5 x Ir thermal memory20 mn short-time pick-up adjustment type IsdAdjustable 9 settings [Isd] short-time pick-up adjustment range1.5...10 x Ir short-time delay adjustment typeAdjustable [tsd] short-time delay adjustment range0…0.4 s I²t=off0.1…0.4 s I²t=on instantaneous pick-up adjustment type IiAdjustable 9 settings instantaneous pick-up adjustment range2...15 x InOff zone selective interlocking ZSIWith communication of dataMeasurement readoutProtection and alarm settings display typeDigital display type of measurementAmmeter Environment ambient air temperature for operation-25…70 °C ambient air temperature for storage-25…85 °C Offer Sustainability REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
User guideFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.