Main rangeMasterpact product nameMasterpact NW product or component typeSwitch disconnector device short nameMasterpact NW50 switch-disconnector nameMasterpact NW50HH device applicationProtection poles description4P network typeAC network frequency50/60 Hz [Ie] rated operational currentAC-23A: 5000 A AC 50/60 Hz 690 V [Ui] rated insulation voltage1000 V AC 50/60 Hz conforming to IEC 60947-3 [Uimp] rated impulse withstand voltage12 kV conforming to IEC 60947-3 [Icm] rated short-circuit making capacity220 kA 690 V AC at 50/60 Hz [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-3 breaking capacity codeHH suitability for isolationYes conforming to IEC 60947-3 contact position indicatorYes visible breakNo pollution degree4 conforming to IEC 60664-1 Complementary control typePush-button mounting modeDrawout mounting supportChassis [Icw] rated short-time withstand current100 kA during 1 s conforming to IEC 60947-3 at 690 V100 kA during 3 s conforming to IEC 60947-4 at 690 V mechanical durability10000 cycles with maintenance conforming to IEC 60947-3 electrical durabilityAC-23A: 1500 cycles 690 V AC 50/60 Hz without maintenance conforming to IEC 60947-3 connection pitch230 mm height352 mm width537 mm depth297 mm net weight160 kg integral instant protection75 kA Environment standardsIEC 60947-3 product certificationsASEFA IP degree of protectionIP30 ambient air temperature for operation-25…70 °C ambient air temperature for storage-40…85 °C Offer Sustainability REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.