View all Nema Pressure Switches
Main range of product9012G pressure sensor typeElectromechanical pressure switch pressure sensor name9012G pressure sensor size275.79 kPa maximum pressure100 psi contacts type and compositionNC-NO, SPDT, Form C, snap action, silver nickel contacts controlled fluidHydraulic oil (-40…250 °F)Non-corrosive liquidsAirNon-corrosive gas fluid connection type0.25 inch 18 NPT conforming to UL 508 pressure switch type of operationDetection of 1 single threshold scale typeFixed differential local displayWithout Complementary range on decreasing pressure6.89…275.79 kPa approx fix differential at mid range1.2 psi +/- 2.5 % full scale cable entry0.5 inch NPT conduit entrance terminal block type4 screw terminals electrical connectionScrew-clamp terminals, AWG 22...AWG 12 electrical circuit typeControl circuit local signallingWithout: [In] rated current6 A 120 V AC0.22 A 125 V DC3 A 240 V AC0.27 A 250 V DC settingInternal enclosure materialThermoplastic pressure actuatorDiaphragm nitrile (Buna-N) height176.28 mm depth69.85 mm width56.13 mm operating positionAny position materials in contact with fluidNitrile (Buna-N)Zinc plated steel short-circuit protection10 A cartridge overload and short-circuit protection, type gL maximum operating rate120 cyc/mn mechanical durability5000000 cycles repeat accuracy4 % net weight0.91 kg Environment vibration resistance2 gn (f= 40…150 Hz) conforming to IEC 68-2-6 shock resistance50 gn conforming to IEC 58-2-27 standardsUL 508CSA C22.2 No 14CE product certificationsCSA LR26817 class 3218 02CEUL listed file E12158 CCN NKPZ NEMA degree of protectionNEMA 1 conforming to UL 50 ambient air temperature for operation-23…85 °C Offer Sustainability REACh Regulation EU RoHS DirectiveNot applicable, out of EU RoHS legal scope Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
EU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.