Main range of productActi9 product nameActi9 iCT product or component typeContactor device short nameICT device applicationLighting Poles3P + N [Ie] rated operational current40 A AC-7A15 A AC-7B pole contact composition4 NO network typeAC control typeRemote control [Uc] control circuit voltage230...240 V AC 50 Hz Complementary network frequency50 Hz [Ue] rated operational voltage220...240 V AC 50 Hz maximum power2.1 W at 220...240 V AC [Ui] rated insulation voltage440 V AC 50 Hz [Uimp] rated impulse withstand voltage4 kV control signal typeMaintained switching frequency100 switching operations/day local signallingAction indicator hold-in power consumption in VA6.5 VA inrush power in VA53 VA mounting modeClip-on mounting support35 mm symmetrical DIN rail 9 mm pitches6 height85 mm width54 mm depth60 mm colourWhite mechanical durability1000000 cycles electrical durability100000 cycles IEC/EN 61095 40 A 50 Hz AC-7A30000 cycles IEC/EN 61095 15 A 50 Hz AC-7B30000 cycles IEC/EN 61095 50 Hz AC-7C100000 cycles EN/IEC 60947-4-1 50 Hz AC-130000 cycles EN/IEC 60947-4-1 50 Hz AC-330000 cycles EN/IEC 60947-4-1 50 Hz AC-5a30000 cycles EN/IEC 60947-4-1 50 Hz AC-5b technology typeDesynchronized neutral pole condition of useLED lighting should be controlled as a group cable entryBottom connections - terminalsControl circuit: tunnel type terminals2 cable(s) 1.5 mm² rigidControl circuit: tunnel type terminals1 cable(s) 1.5…2.5 mm² rigidPower circuit: tunnel type terminals1 cable(s) 6…16 mm² flexiblePower circuit: tunnel type terminals1 cable(s) 6…25 mm² rigidControl circuit: tunnel type terminals2 cable(s) 1.5…2.5 mm² flexible tightening torqueControl circuit: 0.8 N.mPower circuit: 3.5 N.m product compatibilityIACTpIATEtIACTcIACTs compatibility codeICT market segmentResidentialSmall commercial Environment standardsIEC/EN 61095 noise level30 dB heat dissipation2.1 W at 50/60 Hz IP degree of protectionIP20 conforming to IEC 60529IP40 (modular enclosure) conforming to IEC 60529 pollution degree2 tropicalisation2 conforming to EN 60947-4-12 conforming to EN 610952 conforming to IEC 1095 relative humidity95 % at 55 °C operating altitude2000 m ambient air temperature for operation-5…60 °C ambient air temperature for storage-40…60 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight362 g Package 1 Height6 cm Package 1 width11.2 cm Package 1 Length12.1 cm Unit Type of Package 2BB1 Number of Units in Package 24 Package 2 Weight1.53 kg Package 2 Height13 cm Package 2 width12 cm Package 2 Length25 cm Unit Type of Package 3S03 Number of Units in Package 324 Package 3 Weight9.58 kg Package 3 Height30 cm Package 3 width30 cm Package 3 Length40 cm Offer Sustainability Sustainable offer statusGreen Premium product REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 21.4 MBDate 12/11/19DescriptionThis document contains all the knowledge of Schneider Electric around LED Lighting technology. It is built for our professional customers to be used as a reference document, to be shared with newcomers on your field, to be spread around your engineering teams in order to help you raise the optimum architectures. Our engineers are working every day to provide smart solutions to a constantly evolving world.CADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsApplication solutionsFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsMoviesFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages15
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.