Main relay applicationTime delay relay time delay typeDelays de-energizing of a load upon contact closing rangeActi 9 product nameIRT device short nameIRTB signal contacts composition1 C/O Complementary [Ie] rated operational current8 A at 250 V AC8 A at 250 V DC0.01 A at 5 V DC impulse duration> 100 ms local signallingLED, flashing for time delay type of settingRotary knob: time delay configuration time delay range0.1...360000 s accuracy error+/- 10 % repeat accuracy+/- 0.5 % [Uc] control circuit voltage24...240 V AC 50/60 Hz24 V DC [Us] rated supply voltage24...240 V AC at 50/60 Hz24 V DC mounting modeFixed mounting support35 mm symmetrical DIN rail 9 mm pitches2 height93 mm width18 mm depth72 mm net weight0.065 kg colourWhite mechanical durability5000000 cycles electrical durabilityAC-1: 100000 cycles undervoltage behaviour100 ms connections - terminalsTunnel type terminals for 2 cable(s) 1.5 mm² flexible with cable endTunnel type terminals for 2 cable(s) 1.5 mm² flexible without cable endTunnel type terminals for 2 cable(s) 2.5 mm² rigid with cable endTunnel type terminals for 2 cable(s) 2.5 mm² rigid without cable end Environment IP degree of protectionIP20 immunity to microbreaks20 ms ambient air temperature for operation-5…55 °C ambient air temperature for storage-40…70 °C Packing Units Package 1 Weight0.074 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CADFormatSizeDateAdd to My Documentsprp.document.label.format zipSize 758.2 KBDate 7/10/13prp.document.label.format zipSize 2.2 MBDate 1/27/12Instruction sheetFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsEU RoHS DeclarationFormatSizeDateAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.