Main range of productActi 9 product nameActi 9 iPB product or component typePush-button device short nameIPB standardsIEC 60947-5-1IEC 60669-1 Complementary contacts type and composition1 NO [Ie] rated operational current20 A [Ue] rated operational voltage250 V AC control type2 push-button grey mounting modeFixed mounting support35 mm symmetrical DIN rail comb busbar and distribution block compatibilityUpside: ClarioUpside: LibrioUpside: ProDis 9 mm pitches2 height82 mm width18 mm depth71.5 mm colourWhite electrical durabilityAC-22: 30000 cycles AC 50/60 Hz connections - terminalsStaggered tunnel terminal1 cable(s) 0.5 mm² rigidStaggered tunnel terminal1 cable(s) 0.5 mm² flexibleStaggered tunnel terminal1 cable(s) 0.5 mm² flexible with ferruleStaggered tunnel terminal2 cable(s) 2.5 mm² rigidStaggered tunnel terminal2 cable(s) 2.5 mm² flexibleStaggered tunnel terminal2 cable(s) 2.5 mm² flexible with ferrule wire stripping length9 mm tightening torque1 N.m Environment tropicalisation2 relative humidity95 % at 55 °C ambient air temperature for operation-35…70 °C ambient air temperature for storage-40…80 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsApplication solutionsFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.