Main range of productActi 9 product nameActi 9 iPB product or component typePush-button device short nameIPB standardsIEC 60947-5-1IEC 60669-1 Complementary contacts type and composition1 NC [Ie] rated operational current20 A [Ue] rated operational voltage250 V AC control type1 push-button grey local signallingLED indicator red, service life 100000 h of constant lighting efficiency (consumption 0.3 W) signalling circuit voltageAC: 110...230 V 50/60 Hz mounting modeFixed mounting support35 mm symmetrical DIN rail comb busbar and distribution block compatibilityUpside: ClarioUpside: LibrioUpside: ProDis 9 mm pitches2 height82 mm width18 mm depth71.5 mm colourWhite electrical durabilityAC-22: 30000 cycles AC 50/60 Hz connections - terminalsStaggered tunnel terminal1 cable(s) 0.5 mm² rigidStaggered tunnel terminal1 cable(s) 0.5 mm² flexibleStaggered tunnel terminal1 cable(s) 0.5 mm² flexible with ferruleStaggered tunnel terminal2 cable(s) 2.5 mm² rigidStaggered tunnel terminal2 cable(s) 2.5 mm² flexibleStaggered tunnel terminal2 cable(s) 2.5 mm² flexible with ferrule wire stripping length9 mm tightening torque1 N.m Environment tropicalisation2 relative humidity95 % at 55 °C ambient air temperature for operation-35…70 °C ambient air temperature for storage-40…80 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.