Main range of productActi 9 product nameActi 9 iRC product or component typeControl relay device short nameIRCP device applicationPhase control relay signal contacts composition1 C/O Complementary [Ie] rated operational current8 A at 250 V AC (cos Phi = 1) local signallingRed LED for faultIt reports phase loss or reversalGreen LED for power on type of settingRotary knob: asymmetrySelected by wiring: measurement range tripping threshold5...25 % of Us phase asymmetry hysteresis5 % time delay range0.3 s accuracy error+/- 10 % [Us] rated supply voltage400 V AC 50/60 Hz power consumption in VA3 VA mounting modeFixed mounting support35 mm symmetrical DIN rail 9 mm pitches4 height88.1 mm width36 mm depth67 mm net weight0.21 kg colourWhite connections - terminalsTunnel type terminals (top or bottom) 6 cable(s) 1.5 mm² rigid Environment IP degree of protectionIP20 ambient air temperature for operation-5…55 °C ambient air temperature for storage-40…80 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight222 g Package 1 Height4.2 cm Package 1 width8 cm Package 1 Length9.2 cm Unit Type of Package 2S02 Number of Units in Package 236 Package 2 Weight8.591 kg Package 2 Height15 cm Package 2 width30 cm Package 2 Length40 cm Offer Sustainability REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADFormatSizeAdd to My Documentsprp.document.label.format zipSize 1.1 MBDate 7/10/13prp.document.label.format zipSize 2 MBDate 1/27/12Instruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.