- Reason for Substitution: End of life
- Substitution date: 22 November 2017
Main range of productActi 9 product nameActi 9 iPRD product or component typeSurge arrester with pluggable cartridge device short nameIPRD device applicationDistribution poles description3P remote signallingWith signal contacts composition1 SD (1 C/O) surge arrester typeElectrical distribution network earthing systemIT Complementary surge arrester class typeType 2 surge arrester technologyMOV [Ue] rated operational voltage400 V AC (+/- 10 %) at 50/60 Hz [In] nominal discharge currentCommon mode: 20 kA (L/PE) [Imax] maximum discharge currentCommon mode: 65 kA L/PE [Uc] maximum continuous operating voltageCommon mode: 460 V L/PE maximum [Up] voltage protection levelCommon mode <2 kV type 2 L/PE disconnector device typeAssociated circuit breaker iC60N 50 A curve C - Icu 10 kAAssociated circuit breaker iC60H 50 A curve C - Icu 15 kAAssociated circuit breaker NG125N 50 A curve C - Icu 25 kAAssociated circuit breaker NG125H 50 A curve C - Icu 36 kAAssociated circuit breaker NG125L 50 A curve C - Icu 50 kA signalling circuit voltage0.25 A/250 V AC 50/60 Hz mounting modeClip-on mounting supportDIN rail 9 mm pitches6 height81 mm width54 mm depth69 mm net weight0.395 kg colourWhite (RAL 9003) response time<= 25 ns connections - terminalsTunnel type terminal (downside) 2.5…35 mm²Tunnel type terminal (upside) 2.5…35 mm² tightening torque2.5 N.m Environment standardsEN 61643-11IEC 61643-11 product certificationsCE IP degree of protectionIP40 on front face: conforming to IEC 60529IP20 built-in: conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5…90 % operating altitude2000 m ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Packing Units Package 1 Weight0.448 kg Package 1 Height0.700 dm Package 1 width0.600 dm Package 1 Length0.810 dm Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
- All Languages3
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.