A9L16680 is replaced by:
Main range of productActi 9 product nameActi 9 iPRD product or component typeSurge arrester with pluggable cartridge device short nameIPRD8 device applicationDistribution poles description4P remote signallingWithout surge arrester typeElectrical distribution network earthing systemTN-C [Uoc] open circuit voltage10 kV type 3 common mode L/PE10 kV type 3 common mode N/PE Complementary surge arrester class typeType 2 + 3 surge arrester technologyMOV [Ue] rated operational voltage230 V AC (+/- 10 %) at 50/60 Hz 400 V AC (+/- 10 %) at 50/60 Hz [In] nominal discharge currentCommon mode: 2.5 kA (L/PE)Common mode: 2.5 kA (N/PE) [Imax] maximum discharge currentCommon mode: 8 kA L/PECommon mode: 8 kA N/PE [Uc] maximum continuous operating voltageCommon mode: 340 V L/PECommon mode: 340 V N/PE maximum [Up] voltage protection levelCommon mode <1 kV type 2 L/PECommon mode <1 kV type 2 N/PECommon mode <1 kV type 3 L/PECommon mode <1 kV type 3 N/PE [I total] discharge current30 kA disconnector device typeAssociated circuit breaker iC60N 20 A curve C - Icu 10 kAAssociated circuit breaker iC60H 20 A curve C - Icu 15 kAAssociated circuit breaker iC60L 20 A curve C - Icu 25 kA mounting modeClip-on mounting supportDIN rail 9 mm pitches8 height81 mm width72 mm depth69 mm colourWhite (RAL 9003) response time<= 25 ns connections - terminalsTunnel type terminal (downside) 2.5…35 mm²Tunnel type terminal (upside) 2.5…35 mm² tightening torque2.5 N.m Environment standardsEN 61643-11IEC 61643-11 product certificationsCE quality labelsKEMA-KEURNFOVE IP degree of protectionIP40 on front face: conforming to IEC 60529IP20 built-in: conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5…90 % operating altitude2000 m ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Contractual warranty Warranty18 months
- All Languages2
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.