Main rangeProdis product or component typeAdd-on residual current devices device short nameVigi TG40 poles description3P + N neutral positionLeft [In] rated current25 A network typeAC earth-leakage sensitivity300 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType A-SI Complementary device location in systemGroup incomer network frequency50 Hz [Ue] rated operational voltage400 V AC 50 Hz phase to phase residual current tripping technologyVoltage independent [Ui] rated insulation voltage400 V AC 50 Hz conforming to EN 61009-1 [Uimp] rated impulse withstand voltage6 kV conforming to EN 61009-1 local signallingON/OFF indication mounting modeClip-on mounting supportDIN rail electrical connection to mcbBy screws 9 mm pitches6 height82 mm width54 mm depth70 mm product weight210 g colourWhite connections - terminalsCable upstream 0.75…16 mm² rigidCable upstream 0.33…10 mm² flexible wire stripping length13 mm tightening torque2 N.m Environment standardsIEC 60947-2EN 61009-1EN 61009-2-1 IP degree of protectionIP20 conforming to IEC 60529 pollution degree3 conforming to EN 61009-1 tropicalisation2 conforming to IEC 60068-1 relative humidity95 % at 55 °C operating altitude2000 m ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…60 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.