Main rangeClario product or component typeAdd-on residual current devices device short nameVigi C60c poles description4P [In] rated current63 A network typeAC earth-leakage sensitivity300 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType AC Complementary device location in systemGroup incomer network frequency50 Hz [Ue] rated operational voltage400 V AC 50 Hz phase to phase residual current tripping technologyVoltage independent [Ui] rated insulation voltage500 V AC 50 Hz conforming to EN/IEC 61009-1 [Uimp] rated impulse withstand voltage6 kV conforming to EN/IEC 61009-1 local signallingON/OFF indication mounting modeClip-on mounting supportDIN rail electrical connection to mcbBy screws 9 mm pitches6 height82 mm width54 mm depth70 mm net weight210 g colourWhite mechanical durability20000 cycles connections - terminalsCable upstream0.75…16 mm² rigidCable upstream0.33…10 mm² flexible wire stripping length13 mm tightening torque2 N.m Environment standardsEN/IEC 61009-1EN/IEC 61009-2-1 IP degree of protectionIP20 conforming to IEC 60529 pollution degree3 conforming to EN/IEC 61009-1 tropicalisation2 conforming to IEC 60068-1 relative humidity95 % at 55 °C operating altitude2000 m ambient air temperature for operation-5…60 °C ambient air temperature for storage-40…60 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
EU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.