View all Product references for Configurator
Acti 9 iID - RCCB - 4P - 100A - 30mA - type A-GShow more characteristics
has not been replaced. Please contact your customer care center for more information.
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeActi 9 product nameActi 9 iID product or component typeResidual current circuit breaker (RCCB) device short nameIID poles description4P neutral positionLeft [In] rated current100 A network typeAC earth-leakage sensitivity30 mA earth-leakage protection time delayDelayed earth-leakage protection classType A-G Complementary network frequency50/60 Hz [Ue] rated operational voltage380...415 V AC 50/60 Hz rated breaking and making capacityIdm 1500 AIm 1500 A rated conditional short-circuit current10 kA [Ui] rated insulation voltage500 V AC 50/60 Hz [Uimp] rated impulse withstand voltage6 kV contact position indicatorYes control typeToggle mounting modeClip-on mounting supportDIN rail 9 mm pitches8 height91 mm width72 mm depth73 mm net weight0.37 kg colourWhite mechanical durability20000 cycles electrical durabilityAC-1: 10000 cycles locking options descriptionPadlocking device connections - terminalsDouble terminal front1…35 mm² rigidDouble terminal front1…25 mm² flexibleDouble terminal front1…25 mm² flexible with ferruleDouble terminal back1…25 mm² rigidDouble terminal back1…16 mm² flexibleDouble terminal back1…16 mm² flexible with ferrule wire stripping length14 mm for top or bottom connection tightening torque3.5 N.m top or bottom Environment standardsEN/IEC 61008-1 IP degree of protectionIP20 conforming to IEC 60529IP40 (modular enclosure) conforming to IEC 60529 pollution degree3 electromagnetic compatibility8/20 µs impulse withstand, 250 A conforming to EN/IEC 61008-1 ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Contractual warranty Warranty18 months
CADFormatSizeAdd to My Documentsprp.document.label.format zipSize 6.6 MBDate 7/7/11
- All Languages3
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.