Main range of productModicon ABE7 product or component typeSolid state input relay sub-base [Us] rated supply voltage48 V AC 50/60 Hz (sensor end)24 V DC (PLC end) number of channels16 number of terminal per channel2 connections - terminalsScrew type terminals, 1 x 0.09...1 x 1.5 mm², 0.09…1.5 mm² (AWG 28...AWG 16) flexible with cable endScrew type terminals, 1 x 0.14...1 x 2.5 mm², 0.14…2.5 mm² (AWG 26...AWG 12) solidScrew type terminals, 1 x 0.14...1 x 2.5 mm², 0.14…2.5 mm² (AWG 26...AWG 14) flexible without cable endScrew type terminals, 2 x 0.09...2 x 0.75 mm², 0.09…0.75 mm² (AWG 28...AWG 20) flexible with cable endScrew type terminals, 2 x 0.2...2 x 2.5 mm², 0.2…2.5 mm² (AWG 24...AWG 14) solid Complementary terminal block typeRemovable supply voltage limits19…30 V DC (PLC end) conforming to IEC 61131-2 isolation PLC/operative partYes protection typeInternal fuse 1 A 5 x 20 mm fast blow PLC endAdjustable by external fuse fast blow sensor end fixing modeBy clips (35 mm symmetrical DIN rail)By screws (solid plate with fixing kit) current per channel0.012 A current state 1 guaranteed>= 5 mA (sensor end) voltage state 1 guaranteed>= 32 V for sensor end maximum switching current15 mA (PLC end) minimum switching current1 mA for PLC end response time<= 20 ms from state 0 to 1<= 20 ms from state 1 to 0 switching frequency<= 25 Hz duty cycle: 50 % [Uimp] rated impulse withstand voltageIEC 60947-1 2.5 kV [Ui] rated insulation voltage2000 V installation categoryII conforming to IEC 60664-1 tightening torque0.6 N.m with flat Ø 3.5 mm screwdriver net weight0.386 kg Environment dielectric strength2000 V at 50/60 Hz conforming to IEC 60947-1 product certificationsLROS (Lloyds register of shipping)GLDNVBVCSAUL standardsIEC 61131-2 Type 1 IP degree of protectionIP2x conforming to IEC 60529 resistance to incandescent wire750 °C conforming to IEC 60695-2-11 shock resistance15 gn for 11 ms conforming to IEC 60068-2-27 vibration resistance2 gn (f= 10…150 Hz) conforming to IEC 60068-2-6 resistance to electrostatic discharge4 kV (contact) level 3 conforming to IEC 61000-4-28 kV (air) level 3 conforming to IEC 61000-4-2 resistance to radiated fields10 V/m (26000000…1000000000 Hz) conforming to IEC 61000-4-3 level 3 resistance to fast transients2 kV level 3 conforming to IEC 61000-4-4 ambient air temperature for operation-5…60 °C conforming to IEC 61131-2 ambient air temperature for storage-40…80 °C conforming to IEC 61131-2 pollution degree2 conforming to IEC 60664-1 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 350.6 KBDate 1/13/05Instruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsMarine certificateFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensions(1)ABE7BV20 / ABE7BV20E
Mounting and ClearanceMounting
Connections and SchemaHE10 16 ChannelsWiring Diagram
S16E2B1 / E2B1E
S16E2E1 / E2E1E
S16E2E0 / E2E0E
S16E2F0 / E2F0E
S16E2M0 / E2M0E
Performance CurvesCurves for Determining Cable Type and Length According to the Current16-channel Sub-baseLCable lengthITTotal current per sub base (A)IAAverage current per channel (mA)(1)TSXCDP••2 and ABFH20H••0 cables with c.s.a. 0.08 mm2 (AWG 28).(2)TSXCDP••3 cables with c.s.a. 0.34 mm2 (AWG 22).(3)Cables with c.s.a. 0.13 mm2 (AWG 26).
The curves are given for a voltage drop of 1 V in the cable. For n volts tolerance, multiply the length determined from the graph by n.