Main rangePowerLogic product namePowerLogic BCPM product or component typeMulti-circuit energy meter device short nameBCPMA Model typeAdvanced power monitoringBasic instrumentation energy managementSub billing and cost allocation device applicationSub billing power quality analysisvoltage sag and swell detection type of measurementVoltageCurrentFrequencyActive powerPower factorActive energy [Us] rated supply voltage90...277 V AC 50/60 Hz +/- 1 % network frequency60 Hz50 Hz Complementary current transformer inputSolid core CT 100 A42 x update time1.8 s measurement voltage90…277 V phase to neutral150…480 V phase to phase measurement accuracyBranch current 2 % 0.25…2 ABranch current 1 % 2…100 AMains current 3 % 1…100 %Mains current 3 % 2…100 %Voltage 1 % 90…277 V sampling rate256 samples/cycle connection pitch19 mm provided equipment42 x current transformer2 x cables communication port protocolModbus RTU communication port supportRS485 communication of dataLow current alarmHigh current alarmLow-low current alarmUnder voltage alarmHigh-high current alarmOver voltage alarm Environment mounting modePanel-mounted mounting supportEnclosurePanel relative humidity95 % at 0…60 °C ambient air temperature for storage-40…70 °C operating altitude3000 m standardsIEC 61036ANSI C12.1UL 508EN 61010 product certificationsUL width288 mm height146 mm net weight1.5 kg Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsSize pdfSize 56.7 MBDate 9/17/19DescriptionPowerLogic Products Catalogue. Note that no printed catalogues are available but all necessary source files in 14 sections are available for download from the Shopping Kiosk.EU RoHS DeclarationFormatSizeAdd to My DocumentsRoHs China DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.