Main rangePowerLogic product namePowerLogic BCPMSC product or component typeMulti-circuit energy meter device short nameBCPMSCA Model typeAdvanced power monitoringBasic instrumentation energy managementSub billing and cost allocation device applicationSub billing power quality analysisvoltage sag and swell detection type of measurementVoltageCurrentFrequencyActive powerPower factorActive energy [Us] rated supply voltage90...277 V AC 50/60 Hz +/- 1 % network frequency60 Hz50 Hz Complementary current transformer inputSplit core CT 0.333 V60 x update time1.8 s measurement voltage90…277 V phase to neutral150…480 V phase to phase measurement accuracyBranch current 2 % 0.25…2 ABranch current 1 % 2…100 AMains current 3 % 1…100 %Mains current 3 % 2…100 %Voltage 1 % 90…277 V sampling rate256 samples/cycle provided equipment4 x cables4 x adapter board60 x current transformer communication port protocolModbus RTU communication port supportRS485 communication of dataUnder voltage alarmLow-low current alarmOver voltage alarmHigh current alarmLow current alarmHigh-high current alarm Environment mounting modeClip-on mounting supportBoard relative humidity95 % at 0…60 °C ambient air temperature for storage-40…70 °C operating altitude3000 m standardsUL 508EN 61010IEC 61036ANSI C12.1 product certificationsUL width288 mm height146 mm net weight1.5 kg Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsSize pdfSize 56.7 MBDate 9/17/19DescriptionPowerLogic Products Catalogue. Note that no printed catalogues are available but all necessary source files in 14 sections are available for download from the Shopping Kiosk.EU RoHS DeclarationFormatSizeAdd to My DocumentsRoHs China DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.