View all PowerLogic BCPM
BCPM power monitoring advanced + 2 adapter boards - 42 split core CT (not incld)Show more characteristics
has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangePowerLogic product namePowerLogic BCPMSC product or component typeMulti-circuit energy meter device short nameBCPMSCA Model typeAdvanced power monitoringBasic instrumentation energy managementSub billing and cost allocation device applicationSub billing power quality analysisvoltage sag and swell detection type of measurementVoltageCurrentFrequencyActive powerPower factorActive energy [Us] rated supply voltage90...277 V AC 50/60 Hz +/- 1 % network frequency60 Hz50 Hz Complementary current transformer inputSplit core CT 0.333 V42 x update time1.8 s measurement voltage90…277 V phase to neutral150…480 V phase to phase measurement accuracyBranch current 2 % 0.25…2 ABranch current 1 % 2…100 AMains current 3 % 1…100 %Mains current 3 % 2…100 %Voltage 1 % 90…277 V sampling rate256 samples/cycle provided equipment2 x cables2 x adapter boardBracket for support communication port protocolModbus RTU communication port supportRS485 communication of dataHigh current alarmLow current alarmHigh-high current alarmUnder voltage alarmLow-low current alarmOver voltage alarm Environment mounting modeFixed mounting supportBracket relative humidity95 % at 0…60 °C ambient air temperature for storage-40…70 °C operating altitude3000 m standardsEN 61010ANSI C12.1UL 508IEC 61036 product certificationsUL width288 mm height146 mm net weight1.5 kg Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.