Main rangePowerLogic product nameComX product or component typeEnergy server device short nameComX 210 Complementary [Us] rated supply voltageMain supply: 24 V DC maximum power consumption in W26 W 24 V15 W via PoE communication network typeRS485, Modbus serial on 1 RJ45RS485, Modbus serial on terminal blockEthernet, PoE 15W (Power over Ethernet) on 1 RJ45Ethernet, DHCP on 1 RJ45 number of inputs6 digital2 analog discrete input current60 mA at 12 V DC sensor power supply24 V DC at 50 mA analogue input type4...20 mAPt 100Pt 10000...10 V communication gatewayEthernet TCP/IP to Modbus memory capacity128 MB RAM256 MB flash mounting modeClip-on mounting support35 mm DIN rail product certificationsCECULC-TickUL standardsEN 61010-1UL 508EN 60950UL 60950 depth69 mm height109 mm width144 mm net weight450 g local signallingLED: for power supplyLED: for status (GPRS)LED: for communication (Modbus)LED: for communication (Ethernet)LED: for communication (WiFi)LED: for I/O Environment relative humidity5…95 % at 55 °C without condensation IP degree of protectionIP20 (terminal block)IP40 (front face) ambient air temperature for operation-25…70 °C ambient air temperature for storage-40…85 °C pollution degree3 operating altitude2000 m Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My Documentsprp.document.label.format pdfSize 1 MBDate 12/4/19DescriptionThis guide provides recommendations to better secure your Com’X device.Please use this guide in conjunction with the user manual for the step by step procedure details required for the configuration of specific features and settings.NOTE: This guide is applicable for Com'X firmware version 6.5 and above.prp.document.label.format pdfSize 587.2 KBDate 12/4/19DescriptionIt is recommended to procure and install your own Public/Private SSL Certificate to harden your Com’X device. This guide details a multi-step process. The first part of the process involves creating a Com’X compliant certificate file from your SSL certificate & private key. The second part of the process instructs on how to install the certificate on a Com’X.NOTE: This guide is applicable for Com'X firmware version 6.5 and above.prp.document.label.format pdfSize 3.4 MBDate 12/1/19DescriptionCom’X 210 Energy Server User manualprp.document.label.format pdfSize 421.9 KBDate 1/1/17DescriptionThis guide provides an overview of the commissioning process for a new Com'X 510. These guidelines can help reduce commissioning time by eliminating unnecessary reboots and adding device configuration at the optimal time.prp.document.label.format pdfSize 3.5 MBDate 12/1/19DescriptionServeur d’énergie Com’X 210 Manuel de l’utilisateurprp.document.label.format pdfSize 3.5 MBDate 12/1/19DescriptionCom’X 210-Energieserver Benutzerhandbuchprp.document.label.format pdfSize 3.5 MBDate 12/1/19DescriptionServer di energia Com'X 210 Manuale utenteprp.document.label.format pdfSize 3.6 MBDate 12/1/19DescriptionЭнергетический сервер Com'X 210 Руководство пользователяInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages23
Software and FirmwareLanguage
Software - Release NotesFormatSizeAdd to My DocumentsFirmware - ReleasedFormatSizeAdd to My Documentsprp.document.label.format zipSize 47.8 MBDate 2/20/20DescriptionCom’X v6.5.5 supports the following publication platforms:• Energy Operation• Digital Services Platform (DSP)• Comma Separated Values (CSV)If your Com’X 210 device is currently running a firmware version earlier than v2.1, you will first need to upgrade to v2.1 before upgrading to later versions.prp.document.label.format zipSize 40 MBDate 1/29/16DescriptionCom’X firmware upgrade to address bug fixes.Updates:Com’X 200/210Known Issues:1. After upgrading to V2.1.18 from a previous version, the Com’X occasionally fails to communicate toconfigured Zigbee devices on its first startup. To correct this, cycle the power to the Com’X orpress “Restart” on the Maintenance > System Settings page. This is not a reoccurring issue.2. After upgrading to V2.1.18 from a previous version, measurements selected for publication arecleared. To continue to publish, the measurement selections must be reselected.Corrections:1. Corrected issue where after an upgrade to V2.1.17, the Local IDs defaulted to 1, causing loss ofcommunications to devices.2. Corrected issue where after an upgrade to V2.1.17, changing Local IDs in the Settings > ModbusGateway > Device IDs page caused the device to be removed or communications lost.Com’X 510Corrections:1. Corrected the issue of excessive time to load the Measurement Table for the CM4000 and CM3000variants, which also reduced the gateway bandwidth.2. Corrected issue where the data series in the 4 Weeks over 4 Weeks energy dashboard reportsinaccurate Date/Time values when the time zone is configured with a positive offset.3. Updated the on-board User Manual to the correct 2.1 version.
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.