Main range of productAccuSine product nameAccuSine PFV+ product or component typeElectronic VAR controller Complementary Network type3P Network configuration3 or 4 wires network rated voltage208…240 V AC network frequency50/60 Hz +/- 3 % auto-sensing maximum permissible voltage1.1 x Un RMS output current rating60 A reactive power rating25 kvar 240 V AC 50/60 Hz operating modePower factor correctionMains current balancingVolt-var support Installation locationIndoor enclosure mountingWall mounted protection typeWithout protection Heat dissipationRear plenum with forced ventilation for high heat flow electromagnetic compatibilityConducted EMC, class A conforming to EN 61000-6-4 accessibility for operationFront location of connectionBottom Environment Enclosure degree of protectionIP00 environmental characteristicOperating: 3C2 conforming to IEC 60721-3-3Operating: 3S2 conforming to IEC 60721-3-3Storage: 3C3 conforming to IEC 60721-3-3Storage: 3S3 conforming to IEC 60721-3-3 operating altitude<= 1000 m 1 % per 100 m ambient air temperature for operation0…40 °C0…50 °C maximum with current derating of 2 % per °C relative humidity0…95 % PCBA protectionConformal coated standardsCSA C22.2 No 14EN 61000-6-4CSA C22.2 No 60947-1-07EN 60439-1UL 508UL 60947-1 product certificationsRCMABSCECULusDNV-GL ambient air temperature for storage-20…60 °C net weight90 kg height1300 mm width421 mm depth349 mm colourLight grey (RAL 7035)
User guideFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
Software and FirmwareLanguage
FirmwareFormatSizeAdd to My Documentsprp.document.label.format zipSize 19.9 MBDate 4/10/20DescriptionThe purpose of this document is to provide users, installers, and maintenance personnel with the firmware upgrade procedure needed to maintain the AccuSine PCSn.Please download the .zip file and then unzip on your computer. Read the instructions carefully and become familiar with the device before executing this procedure.
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.