Main range of productEasy9 product or component typeResidual current circuit breaker (RCCB) device short nameEasy9 RCCB Poles2P neutral positionLeft [In] rated current63 A network typeAC earth-leakage sensitivity100 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType A rated breaking and making capacity500 A rated conditional short-circuit currentEasy9 MCB: 4500 A 63 A Complementary device location in systemOutgoer network frequency50 Hz [Ue] rated operational voltage230 V AC 50 Hz residual current tripping technologyVoltage dependent [Ui] rated insulation voltage440 V AC [Uimp] rated impulse withstand voltage4 kV contact position indicatorYes control typeToggle mounting modeClip-on mounting supportDIN rail comb busbar and distribution block compatibilityTop: YES 9 mm pitches4 height82 mm width36 mm depth72 mm colourGrey (RAL 7035) mechanical durability5000 cycles electrical durabilityAC: 2000 cycles 230 V AC 50 Hz connections - terminalsTunnel type terminal (top or bottom) 1…25 mm² rigidTunnel type terminal (top or bottom) 1…16 mm² flexible tightening torque2.5 N.m top or bottom market segmentSmall commercialResidential Environment standardsIEC 61008-1 product certificationsEACGOST-RCE pollution degree2 conforming to IEC 61008-1 tropicalisation2 relative humidity95 % at 55 °C ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
EU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.