Main range of productCanalis range compatibilityKN busbar trunking product or component typeTap-off unit busbar trunking compatibilityCanalis KN busbar trunkingplug-in [Ie] rated operational current16 A protection typeCircuit breaker: iC60N mounting modePlug-in with phase selection tap-off unit polarityL+N+PE colourWhite (RAL 9001) Complementary device applicationLow power distribution provided equipmentcircuit breaker cable clamp [Ue] rated operational voltage230...500 V depending on protective device [Uimp] rated impulse withstand voltage4.6 kV [Ui] rated insulation voltage400 V depending on protective device500 V depending on protective device network frequency50/60 Hz electrical connectionCable clamp terminal 4 mm² flexibleCable clamp terminal 6 mm² rigid door/cover opening sideFront tap-off unit disconnection modeBy drawing out standardsIEC 61439-6IEC 61439-1 width79 mm depth70 mm height172 mm net weight0.34 kg Environment earthing systemTTTN-S IP degree of protectionIP41 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages13
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.