Main range of productCanalis range compatibilityKN busbar trunking product or component typeTap-off unit busbar trunking compatibilityCanalis KN busbar trunkingplug-in [Ie] rated operational current20 A at 35 °C protection typefuse isolator: BS88 fuse, size A1 conforming to BS provided equipmentfuse to be ordered separately cable clamp mounting modePlug-in with fixed polarity tap-off unit polarity3L+PE3L+N+PE colourWhite (RAL 9001) Complementary device applicationLow power distribution [Ue] rated operational voltage230...500 V depending on protective device [Uimp] rated impulse withstand voltage4.6 kV [Ui] rated insulation voltage500 V depending on protective device network frequency50/60 Hz electrical connectionCable clamp terminal - ISO32 4 mm² flexibleCable clamp terminal - ISO32 6 mm² rigid door/cover opening sideFront tap-off unit disconnection modeBy drawing out standardsIEC 61439-1IEC 61439-6 width135 mm depth90 mm height165 mm net weight0.6 kg Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Halogen content performanceHalogen free product Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.