Main range of productCanalis range compatibilityKT busbar trunkingKS busbar trunking product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunkingplug-inCanalis KT busbar trunking with KS type plug-in [Ie] rated operational current50 A at 35 °C protection typefuse isolator: Neozed fuse, size E18 conforming to DIN provided equipmentfuse to be ordered separately mounting modePlug-in with fixed polarity tap-off unit polarity3L+PEN colourWhite (RAL 9001) Complementary device applicationMedium power distribution [Ue] rated operational voltage230...690 V depending on protective device [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage500 V depending on protective device network frequency50/60 Hz electrical connectionCable clamp terminal - ISO50 25 mm² flexibleCable clamp terminal - ISO50 25 mm² rigid door/cover opening sideRight tap-off unit disconnection modeBy opening the door standardsIEC 61439-1IEC 61439-6 body materialPlastic width356 mm depth103 mm depth (door open)432.5 mm height167 mm net weight2.4 kg Environment earthing systemTN-C IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages18
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.