Main rangeCanalis product nameKT product or component typeExpansion unit busbar descriptionFlexible bar device short nameKTA device applicationFeeder length materialAluminium [Ie] rated operational current2000 A at 35 °C polarity3L + PE number of tap-off outlets0 length1000 mm provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current110 kA [Ipk] rated peak withstand current242 kA radiated magnetic field1.3 µT thermal stress limit4900 A².s THDI0…15 % 2000 A15…33 % 2500 A33…100 % 3200 A maximum voltage drop<0.0029 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.003 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0029 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.0027 V with power factor = 0.7 at 50 Hz with 1A for 100 m long mounting modeBy hook mounting supportCantilever armPendant installation directionVerticalHorizontal horizontal distance30 m neutral positionRight standardsIEC 61439-1IEC 61439-6 dimension typeFix width140 mm height204 mm colourWhite (RAL 9001) net weight22 kg linear load22 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (97 % of In)40…45 °C (93 % of In)45…50 °C (90 % of In)50…55 °C (86 % of In)
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsSize zipSize 901.2 KBDate 1/14/14Size zipSize 841.1 KBDate 1/14/14Size zipSize 868.1 KBDate 1/14/14Size zipSize 646.5 KBDate 1/7/14CertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
- All Languages16
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.