Main rangeCanalis product nameKT product or component typeMultiple elbow busbar descriptionStandard device short nameKTC device applicationChange direction materialCopper [Ie] rated operational current1000 A at 35 °C polarity3L + N + PER direction change typedirection 2: edgewise to upward direction 1: flat to left operating angle90 ° earth conductorReinforced short-circuit levelReinforced version provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current65 kA [Ipk] rated peak withstand current143 kA radiated magnetic field0.4 µT thermal stress limit4225 A².s THDI0…15 % 1000 A maximum voltage drop<0.0043 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.0047 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0046 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.0044 V with power factor = 0.7 at 50 Hz with 1A for 100 m long neutral positionRight standardsIEC 61439-6IEC 61439-1 dimension typeMade to measure width140 mm heightdirection 2: 195…574 mm colourWhite (RAL 9001) lengthdirection 1: 300 mm direction 3: 275 mm linear load25 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (95 % of In)40…45 °C (90 % of In)45…50 °C (84 % of In)50…55 °C (79 % of In)
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 901.1 KBDate 1/14/14CertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.