Main rangeCanalis product nameKT product or component typeCenter feeder trunking device short nameKTC device applicationFeeder length supplyDry-type transformer materialCopper [Ie] rated operational current1350 A at 35 °C neutral positionLeft earth conductorStandard earth short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current50 kA [Ipk] rated peak withstand current110 kA radiated magnetic field0.5 µT thermal stress limit2500 A².s THDI15…33 % 1000 A0…15 % 1350 A maximum voltage drop<0.0031 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.0034 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0033 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.0031 V with power factor = 0.7 at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PE number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure connection pitch390…700 mm bar width160 mm depth140 mm height364 mm lengthdirection 1: 260 mm1680 mm colourWhite (RAL 9001) linear load33 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (95 % of In)40…45 °C (90 % of In)45…50 °C (84 % of In)50…55 °C (79 % of In) Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight36.15 kg Package 1 Height28 cm Package 1 width13.8 cm Package 1 Length190 cm
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 426.4 KBDate 1/14/14CertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.