KTC1600ED320 may be replaced by any of the following products:
Main rangeCanalis product nameKT product or component typeBusbar trunking busbar descriptionDistribution length device short nameKTC device applicationHigh power distribution materialCopper [Ie] rated operational current1600 A at 35 °C polarity3L + PE number of tap-off outlets3 nominal output current25…630 A earth conductorStandard earth short-circuit levelStandard version length2000 mm provided equipmentTrunking unitJointing unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current65 kA [Ipk] rated peak withstand current143 kA electrical connectionSliding contact radiated magnetic field0.75 µT thermal stress limit4225 A².s THDI0…15 % 1600 A15…33 % 1350 A33…100 % 1000 A maximum voltage drop<0.0027 V with power factor = 0.7 at 50 Hz with 1A for 100 m long <0.0026 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.0029 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0028 V with power factor = 0.8 at 50 Hz with 1A for 100 m long mounting modeBy hook mounting supportPendantCantilever arm installation directionVerticalHorizontal neutral positionRight tap-off unit interval500 mm standardsIEC 61439-6IEC 61439-1 dimension typeFix width140 mm height124 mm colourWhite (RAL 9001) net weight58 kg linear load29 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (95 % of In)40…45 °C (90 % of In)45…50 °C (84 % of In)50…55 °C (79 % of In)
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My Documents
- All Languages5
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.