Main rangeCanalis product nameKT product or component typeElbow busbar descriptionStandard device short nameKTC device applicationChange direction materialCopper [Ie] rated operational current2000 A at 35 °C polarity3L + PE direction change typedirection 1: edgewise to upward operating angle90 ° earth conductorStandard earth short-circuit levelStandard version provided equipmentJointing unitTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current110 kA [Ipk] rated peak withstand current242 kA radiated magnetic field0.9 µT thermal stress limit4900 A².s THDI15…33 % 1600 A0…15 % 2000 A33…100 % 1350 A maximum voltage drop<0.0019 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.0022 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0022 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.0021 V with power factor = 0.7 at 50 Hz with 1A for 100 m long neutral positionRight standardsIEC 61439-6IEC 61439-1 dimension typeMade to measure short branch width140 mm height164 mm lengthdirection 1: 230 mm direction 1: 321…819 mm colourWhite (RAL 9001) linear load36 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (95 % of In)40…45 °C (90 % of In)45…50 °C (84 % of In)50…55 °C (79 % of In)
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.