Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive load utilisation categoryAC-1 poles description4P power pole contact composition4 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current350 A (at <40 °C) at <= 440 V AC AC-1 [Uc] control circuit voltage48 V AC 40...400 Hz Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current350 A (at 40 °C) rated breaking capacity2120 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current2200 A 40 °C - 10 s1230 A 40 °C - 30 s950 A 40 °C - 1 min620 A 40 °C - 3 min480 A 40 °C - 10 min associated fuse rating315 A aM at <= 440 V400 A gG at <= 440 V average impedance0.3 mOhm - Ith 350 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole37 W AC-1 mounting supportPlate standardsIEC 60947-1IEC 60947-4-1JIS C8201-4-1EN 60947-4-1EN 60947-1 product certificationsDNVLROS (Lloyds register of shipping)ABSRMRoSCBBVRINACCCUL connections - terminalsControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: bar 2 cable(s) - busbar cross section: 32 x 4 mmPower circuit: lugs-ring terminals 1 cable(s) 240 mm²Power circuit: connector 1 cable(s) 240 mm²Power circuit: bolted connection tightening torqueControl circuit: 1.2 N.mPower circuit: 35 N.m control circuit voltage limitsOperational: 0.85...1.1 Uc 40...400 Hz (at 55 °C)Drop-out: 0.15...0.2 Uc 40...400 Hz (at 55 °C) inrush power in VA650 VA 40...400 Hz cos phi 0.9 (at 20 °C) hold-in power consumption in VA10 VA 40...400 Hz cos phi 0.9 (at 20 °C) heat dissipation8 W operating time40...65 ms closing100...170 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 55 °C compatibility codeLC1F Environment IP degree of protectionIP20 front face with shrouds conforming to IEC 60529IP20 front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C height203 mm width244.5 mm depth213 mm net weight8.54 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 111.5 MBDate 7/12/19DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...).The catalogue can also be downloaded chapter per chapter.CADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documentsprp.document.label.format pdfSize 989.9 KBDate 12/1/09DescriptionModbus SL com interface, ULP ModuleChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages19
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.