Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive load utilisation categoryAC-1 poles description4P power pole contact composition4 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current400 A (at <40 °C) at <= 440 V AC AC-1 [Uc] control circuit voltage400 V AC 40...400 Hz Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current400 A (at 40 °C) rated breaking capacity2640 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current2650 A 40 °C - 10 s1800 A 40 °C - 30 s1300 A 40 °C - 1 min900 A 40 °C - 3 min750 A 40 °C - 10 min associated fuse rating400 A aM at <= 440 V500 A gG at <= 440 V average impedance0.28 mOhm - Ith 400 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole44 W AC-1 mounting supportPlate standardsEN 60947-4-1EN 60947-1JIS C8201-4-1IEC 60947-1IEC 60947-4-1 product certificationsCCCRINAULBVLROS (Lloyds register of shipping)CBDNVABSRMRoS connections - terminalsControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: lugs-ring terminals 1 cable(s) 240 mm²Power circuit: bar 2 cable(s) - busbar cross section: 30 x 5 mmPower circuit: bolted connection tightening torqueControl circuit: 1.2 N.mPower circuit: 35 N.m control circuit voltage limitsOperational: 0.85...1.1 Uc 40...400 Hz (at 55 °C)Drop-out: 0.35...0.55 Uc 40...400 Hz (at 55 °C) inrush power in VA650 VA 40...400 Hz cos phi 0.9 (at 20 °C) hold-in power consumption in VA10 VA 40...400 Hz cos phi 0.9 (at 20 °C) heat dissipation8 W operating time40...65 ms closing100...170 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 55 °C compatibility codeLC1F Environment IP degree of protectionIP20 front face with shrouds conforming to IEC 60529IP20 front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C height206 mm width261 mm depth219 mm net weight9.5 kg Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight11.03 kg Package 1 Height25.5 cm Package 1 width23.5 cm Package 1 Length29 cm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 111.5 MBDate 7/12/19DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...).The catalogue can also be downloaded chapter per chapter.CADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages17
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.