View all TeSys F
TeSys F contactor - 3P (3 NO) - AC-3 - <= 440 V 400 A - coil 400 V DCShow more characteristics
LC1F400VD has not been replaced. Please contact your customer care center for more information.
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationResistive loadMotor control utilisation categoryAC-1AC-4AC-3 poles description3P power pole contact composition3 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current500 A (at <40 °C) at <= 440 V AC AC-1400 A (at <55 °C) at <= 440 V AC AC-3 motor power kW75 kW at 400 V AC 50/60 Hz (AC-4)200 kW at 380...400 V AC 50/60 Hz (AC-3)220 kW at 415 V AC 50/60 Hz (AC-3)250 kW at 440 V AC 50/60 Hz (AC-3)257 kW at 500 V AC 50/60 Hz (AC-3)280 kW at 660...690 V AC 50/60 Hz (AC-3)185 kW at 1000 V AC 50/60 Hz (AC-3)110 kW at 220...230 V AC 50/60 Hz (AC-3) [Uc] control circuit voltage400 V DC coil typeStandard Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current500 A (at 40 °C) rated breaking capacity3200 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current3600 A 40 °C - 10 s2400 A 40 °C - 30 s1700 A 40 °C - 1 min1200 A 40 °C - 3 min1000 A 40 °C - 10 min associated fuse rating400 A aM at <= 440 V500 A gG at <= 440 V average impedance0.26 mOhm - Ith 500 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole65 W AC-142 W AC-3 mounting supportPlate standardsJIS C8201-4-1EN 60947-4-1IEC 60947-1EN 60947-1IEC 60947-4-1 product certificationsLROS (Lloyds register of shipping)CCCDNVRINACBABSULBVRMRoS connections - terminalsControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: bar 2 cable(s) - busbar cross section: 30 x 5 mmPower circuit: lugs-ring terminals 2 cable(s) 150 mm²Power circuit: bolted connection tightening torqueControl circuit: 1.2 N.mPower circuit: 35 N.m control circuit voltage limitsOperational: 0.85...1.1 Uc (at 55 °C)Drop-out: 0.2...0.35 Uc (at 55 °C) inrush power in W1000 W (at 20 °C) hold-in power consumption in W6 W at 20 °C heat dissipation6 W operating time50...60 ms closing45...60 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 55 °C compatibility codeLC1F Environment IP degree of protectionIP20 front face with shrouds conforming to IEC 60529IP20 front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C height206 mm width213 mm depth219 mm net weight9.1 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsBrochureFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.