View all TeSys K
TeSys K changeover contactor - 4P - AC-1 <= 440 V 20 A - 220...230 VAC coilShow more characteristics
has not been replaced. Please contact your customer care center for more information.
The maximum number of products that can be compared is 4
Main rangeTeSys product nameTeSys K product or component typeChangeover contactor device short nameLC8K device applicationControl contactor applicationResistive load utilisation categoryAC-1 device presentationPreassembled with reversing power busbar poles description4P power pole contact composition4 NO [Ue] rated operational voltagePower circuit: 690 V AC 50/60 Hz [Ie] rated operational current20 A (at <50 °C) at <= 440 V AC AC-1for power circuit16 A (at <70 °C) at 690 V AC AC-1for power circuit control circuit typeAC at 50/60 Hz silent [Uc] control circuit voltage220...230 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current20 A (at 50 °C)for power circuit Irms rated making capacity110 A ACfor power circuit conforming to NF C 63-110110 A ACfor power circuit conforming to IEC 60947 rated breaking capacity110 A at 415 V conforming to IEC 60947110 A at 440 V conforming to IEC 6094780 A at 500 V conforming to IEC 60947110 A at 220...230 V conforming to IEC 60947110 A at 380...400 V conforming to IEC 6094770 A at 660...690 V conforming to IEC 60947 [Icw] rated short-time withstand current90 A 50 °C - 1 sfor power circuit85 A 50 °C - 5 sfor power circuit80 A 50 °C - 10 sfor power circuit60 A 50 °C - 30 sfor power circuit45 A 50 °C - 1 minfor power circuit40 A 50 °C - 3 minfor power circuit20 A 50 °C - >= 15 minfor power circuit associated fuse rating25 A gG at <= 440 Vfor power circuit25 A aMfor power circuit average impedance3 mOhm - Ith 20 A 50 Hzfor power circuit [Ui] rated insulation voltagePower circuit: 600 V conforming to UL 508Power circuit: 690 V conforming to IEC 60947-4-1Power circuit: 600 V conforming to CSA C22.2 No 14 electrical durability0.18 Mcycles 20 A AC-1 at Ue <= 440 V1.3 Mcycles 9 A AC-3 at Ue <= 440 V interlocking typeMechanical mounting supportPlateRail standardsVDE 0660BS 5424NF C 63-110IEC 60947 product certificationsULCSA connections - terminalsSolder pins - busbar cross section: 1.5 x 0.9 mm operating time30...40 ms coil energisation and NO closing30 ms coil de-energisation and NO opening safety reliability levelB10d = 1369863 cycles contactor with nominal load conforming to EN/ISO 13849-1B10d = 20000000 cycles contactor with mechanical load conforming to EN/ISO 13849-1 mechanical durability5 Mcycles maximum operating rate3600 cyc/h Complementary control circuit voltage limitsOperational: 0.85...1.1 Uc (at <50 °C)Drop-out: 0.1...0.75 Uc (at <50 °C) inrush power in VA3 VA (at 20 °C) hold-in power consumption in VA3 VA (at 20 °C) heat dissipation3 W Environment IP degree of protectionIP20 conforming to VDE 0106 protective treatmentTC conforming to IEC 60068TC conforming to DIN 50016 ambient air temperature for operation-25…50 °C ambient air temperature for storage-50…80 °C operating altitude2000 m without derating flame retardanceV1 conforming to UL 94Requirement 2 conforming to NF F 16-101Requirement 2 conforming to NF F 16-102 mechanical robustnessShocks contactor closed, on X axis: 10 Gn for 11 ms conforming to IEC 60068-2-27Shocks contactor closed, on Y axis: 15 Gn for 11 ms conforming to IEC 60068-2-27Shocks contactor closed, on Z axis: 15 Gn for 11 ms conforming to IEC 60068-2-27Shocks contactor opened, on X axis: 6 Gn for 11 ms conforming to IEC 60068-2-27Shocks contactor opened, on Y axis: 10 Gn for 11 ms conforming to IEC 60068-2-27Shocks contactor opened, on Z axis: 10 Gn for 11 ms conforming to IEC 60068-2-27Vibrations contactor closed: 4 Gn, 5...300 Hz conforming to IEC 60068-2-6Vibrations contactor opened: 2 Gn, 5...300 Hz conforming to IEC 60068-2-6 height58 mm width90 mm depth57 mm net weight0.47 kg Contractual warranty Warranty18 months
- All Languages1
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.