Main rangeTeSys product nameTeSys LE device short nameLE4K product or component typeEnclosed DOL starter device applicationStandard materialPolycarbonate utilisation categoryAC-3 device compositionThermal overload relay ordered separatelyContactorFuse disconnector [Ie] rated operational current9 A AC-3 motor power kW4 kW at 380/400 V AC 50/60 Hz4 kW at 415 V AC 50/60 Hz4 kW at 440 V AC 50/60 Hz2.2 kW at 220/230 V AC 50/60 Hz [Uc] control circuit voltage400 V AC 50/60 Hz [Ithe] conventional enclosed thermal current9 A associated fuse rating12 A 10 x 38 mm aM control typePush-button start green IPush-button stop/reset red O Complementary cable entry number4 ISO20 top4 2 Pg 13 + 2 Pg 16 top4 ISO20 bottom4 2 Pg 13 + 2 Pg 16 bottom width175 mm height165 mm depth146 mm net weight1.45 kg Environment IP degree of protectionIP65 conforming to IEC 60529 IK degree of protectionIK09 conforming to IEC 60529 standardsIEC 60947-4-1 ambient air temperature for operation-5…40 °C environmental characteristicStandard environment Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 111.5 MBDate 7/12/19DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...).The catalogue can also be downloaded chapter per chapter.Instruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.