Main range of productTeSys K rangeTeSys product or component typeContactor device short nameLP1K contactor applicationResistive load utilisation categoryAC-1 poles description4P pole contact composition4 NO [Ie] rated operational current20 A (at <50 °C) at <= 440 V AC AC-1 for power circuit16 A (at <70 °C) at 690 V AC AC-1 for power circuit Complementary control circuit voltage limitsOperational: 0.8...1.15 Uc (at <50 °C)Drop-out: 0.1...0.75 Uc (at <50 °C) [Ui] rated insulation voltagePower circuit: 600 V conforming to UL 508Power circuit: 690 V conforming to IEC 60947-4-1Power circuit: 600 V conforming to CSA C22.2 No 14 [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII mounting supportRailPlate flame retardanceV1 conforming to UL 94Requirement 2 conforming to NF F 16-101Requirement 2 conforming to NF F 16-102 tightening torque1.3 N.m - on screw clamp terminals - with screwdriver Philips No 21.3 N.m - on screw clamp terminals - with screwdriver flat Ø 6 mm [Ue] rated operational voltagePower circuit: 690 V AC 50/60 Hz [Ith] conventional free air thermal current20 A (at 50 °C) for power circuit Irms rated making capacity110 A AC for power circuit conforming to NF C 63-110110 A AC for power circuit conforming to IEC 60947 rated breaking capacity110 A at 415 V conforming to IEC 60947110 A at 440 V conforming to IEC 6094780 A at 500 V conforming to IEC 60947110 A at 220...230 V conforming to IEC 60947110 A at 380...400 V conforming to IEC 6094770 A at 660...690 V conforming to IEC 60947 associated fuse rating25 A gG at <= 440 V for power circuit25 A aM for power circuit average impedance3 mOhm - Ith 20 A 50 Hz for power circuit inrush power in W3 W (at 20 °C) hold-in power consumption in W3 W at 20 °C operating time30...40 ms coil energisation and NO closing10 ms coil de-energisation and NO opening safety reliability levelB10d = 1369863 cycles contactor with nominal load conforming to EN/ISO 13849-1B10d = 20000000 cycles contactor with mechanical load conforming to EN/ISO 13849-1 mechanical durability10 Mcycles maximum operating rate3600 cyc/h height58 mm width45 mm depth57 mm net weight0.225 kg Environment product certificationsULCSA ambient air temperature for operation-25…50 °C ambient air temperature for storage-50…80 °C operating altitude2000 m without derating Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight225 g Package 1 Height6.6 cm Package 1 width6.6 cm Package 1 Length6.6 cm Offer Sustainability Sustainable offer statusGreen Premium product REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeDateAdd to My Documentsprp.document.label.format pdfSize 118.2 MBDate 7/22/20DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...). This edition includes a presentation of the new TeSys island system. The catalogue can also be downloaded chapter per chapter.prp.document.label.format pdfSize 16.1 MBDate 7/22/20DescriptionContactors : TeSys D.Mini contactors, pre cabled reversing contactors : TeSys SK, KModular (on DIN rail) contactors, dual tariif contactors, impulse relays :TeSys SKGC, GC, GY, GFAccessoriesCADFormatSizeDateAdd to My DocumentsCertificateFormatSizeDateAdd to My DocumentsInstruction sheetFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My DocumentsEnd of Life InformationFormatSizeDateAdd to My DocumentsEU RoHS DeclarationFormatSizeDateAdd to My Documents
- All Languages13
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.