Main range of productNSX100...250 product or component typeTrip unit range compatibilityCompact NSX100Compact NSX160Compact NSX250 device applicationDistribution poles description4P protected poles description3t neutral positionLeft network typeAC network frequency50/60 Hz trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI protection typeL : for overload protection (thermal)I : for short-circuit protection (magnetic) trip unit rating80 A at 40 °C Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz neutral protection settingNo protection long time pick-up adjustment type IrAdjustable [Ir] long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120…400 s at 1.5 x In15 s at 6 x Ir short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range640 A short-time delay adjustment typeFixed Environment standardsUL 508EN/IEC 60947-2 product certificationsEACMarineCCC ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.