Main range of productNSX100...250 product or component typeTrip unit range compatibilityCompact NSX100Compact NSX100 DC device applicationGenerator poles description3P protected poles description2t network typeACDC network frequency50/60 Hz trip unit nameTM-G trip unit technologyThermal-magnetic trip unit protection functionsLI protection typeL : for overload protection (thermal)I : for short-circuit protection (magnetic) trip unit rating16 A at 40 °C Complementary mounting modeFixed [Ue] rated operational voltage690 V AC 50/60 Hz750 V DC long time pick-up adjustment type IrAdjustable [Ir] long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120…400 s at 1.5 x In short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range63 A short-time delay adjustment typeFixed Environment standardsUL 508EN/IEC 60947-2 product certificationsCCCMarineEAC ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight353 g Package 1 Height6.7 cm Package 1 width9.7 cm Package 1 Length11 cm Unit Type of Package 2S03 Number of Units in Package 228 Package 2 Weight10.371 kg Package 2 Height30 cm Package 2 width30 cm Package 2 Length40 cm Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.