Main rangeCompact product nameCompact NSX range of productNSX100...250 device short nameCompact NSX100F product or component typeCircuit breaker device applicationDistribution poles description4P protected poles description3t neutral positionLeft [In] rated current25 A at 40 °C [Ue] rated operational voltage690 V AC 50/60 Hz network typeAC network frequency50/60 Hz suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 utilisation categoryCategory A [Icu] rated ultimate short-circuit breaking capacity10 kA at 600 V AC 50/60 Hz conforming to UL 50825 kA at 480 V AC 50/60 Hz conforming to UL 50885 kA at 240 V AC 50/60 Hz conforming to UL 50822 kA Icu at 525 V AC 50/60 Hz conforming to IEC 60947-225 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-235 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-236 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-28 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-285 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-2 Performance levelF 36 kA 415 V AC trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI control typeToggle Circuit breaker mounting modeFixed Complementary [Ui] rated insulation voltage800 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ics] rated service short-circuit breaking capacity11 kA at 525 V AC 50/60 Hz conforming to IEC 60947-235 kA at 440 V AC 50/60 Hz conforming to IEC 60947-236 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-24 kA at 660/690 V AC 50/60 Hz conforming to IEC 60947-285 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-212.5 kA at 500 V AC 50/60 Hz conforming to IEC 60947-2 mechanical durability50000 cycles mounting supportBackplate upside connectionFront downside connectionFront protection typeL : for overload protection (thermal)I : for short-circuit protection (magnetic) trip unit rating25 A at 40 °C Long-time pick-up adjustment type Ir (thermal protection)Adjustable [Ir] long-time protection pick-up adjustment range0.7...1 x In Long-time protection delay adjustment type trFixed [tr] long-time protection delay adjustment range120…400 s at 1.5 x In15 s at 6 x Ir Short-time protection pick-up adjustment type IsdFixed [Isd] Short-time protection pick-up adjustment range300 A Short-time protection delay adjustment type tsdFixed Neutral protection settingsNo protection (3t) auxiliary contact compositionWithout Width (W)140 mm Height (H)161 mm Depth (D)86 mm net weight2.4 kg Environment standardsEN/IEC 60947UL 508 product certificationsEACMarineCCC overvoltage categoryClass II electrical shock protection classClass II pollution degree3 conforming to IEC 60664-1 IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 ambient air temperature for operation-35…70 °C ambient air temperature for storage-55…85 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight2.349 kg Package 1 Height14.5 cm Package 1 width17.16 cm Package 1 Length19 cm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeDateAdd to My DocumentsUser guideFormatSizeDateAdd to My DocumentsCADFormatSizeDateAdd to My Documentsprp.document.label.format zipSize 1.9 MBDate 6/22/12prp.document.label.format zipSize 7 MBDate 8/4/08prp.document.label.format zipSize 6.2 MBDate 8/4/08Instruction sheetFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My DocumentsEU RoHS DeclarationFormatSizeDateAdd to My Documents
- All Languages16
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.