Main rangeCompact product nameCompact NSX product or component typeCircuit breaker device short nameCompact NSX100H device applicationDistribution poles description4P protected poles description4t neutral positionLeft network typeAC network frequency50/60 Hz [In] rated current16 A at 40 °C [Ui] rated insulation voltage800 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ue] rated operational voltage690 V AC 50/60 Hz Breaking capacity codeH 70 kA 415 V AC breaking capacity10 kA at 600 V AC 50/60 Hz conforming to UL 50885 kA at 240 V AC 50/60 Hz conforming to UL 50865 kA at 480 V AC 50/60 Hz conforming to UL 50810 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-2100 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-235 kA Icu at 525 V AC 50/60 Hz conforming to IEC 60947-250 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-265 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-270 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity10 kA at 660/690 V AC 50/60 Hz conforming to IEC 60947-2100 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-235 kA at 525 V AC 50/60 Hz conforming to IEC 60947-250 kA at 500 V AC 50/60 Hz conforming to IEC 60947-265 kA at 440 V AC 50/60 Hz conforming to IEC 60947-270 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-2 suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 utilisation categoryCategory A trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI pollution degree3 conforming to IEC 60664-1 Complementary control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront auxiliary contact compositionWithout mechanical durability50000 cycles electrical durability10000 cycles 690 V In conforming to IEC 60947-220000 cycles 690 V In/2 conforming to IEC 60947-230000 cycles 440 V In conforming to IEC 60947-250000 cycles 440 V In/2 conforming to IEC 60947-2 connection pitch35 mm local signallingPositive contact indication neutral protection setting1 x Ir (4t) protection typeL : for overload protection (thermal)I : for short-circuit protection (magnetic) trip unit rating16 A at 40 °C long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120…400 s at 1.5 x In15 s at 6 x Ir short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range190 A short-time delay adjustment typeFixed height161 mm width140 mm depth86 mm product weight2.4 kg compatibility codeNSX100 Environment overvoltage categoryClass II electrical shock protection classClass II standardsEN/IEC 60947UL 508 product certificationsMarineCCCEAC IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 ambient air temperature for operation-35…70 °C ambient air temperature for storage-55…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsSize zipSize 1.6 MBDate 1/5/01Size pdfSize 253.9 KBDate 10/24/18DescriptionYou will be redirected to the Traceparts website. Register for free or log in to your Traceparts account to download more than 15 different 2D or 3D CAD formats.Size zipSize 1.9 MBDate 6/22/12Size zipSize 6.2 MBDate 8/4/08Size zipSize 7 MBDate 8/3/08Instruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages18
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.