Main rangeCompact product nameCompact NSX product or component typeCircuit breaker with Vigi add-on device short nameVigiCompact NSX100B device applicationDistribution poles description4P protected poles description4t neutral positionLeft network typeAC network frequency50/60 Hz [In] rated current80 A at 40 °C [Ui] rated insulation voltage800 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ue] rated operational voltage440 V AC 50/60 Hz Breaking capacity codeB 25 kA 415 V AC breaking capacity15 kA Icu at 500 V AC 50/60 Hz conforming to IEC 60947-220 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-225 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-240 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity20 kA at 440 V AC 50/60 Hz conforming to IEC 60947-225 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-240 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-27.5 kA at 500 V AC 50/60 Hz conforming to IEC 60947-2 suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 utilisation categoryCategory A trip unit nameTM-D trip unit technologyThermal-magnetic trip unit protection functionsLI earth-leakage add-on module nameMH pollution degree3 conforming to IEC 60664-1 Complementary control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront mechanical durability50000 cycles electrical durability10000 cycles 690 V In conforming to IEC 60947-220000 cycles 690 V In/2 conforming to IEC 60947-230000 cycles 440 V In conforming to IEC 60947-250000 cycles 440 V In/2 conforming to IEC 60947-2 connection pitch35 mm local signallingPositive contact indication neutral protection setting1 x Ir (4t) protection typeL : for overload protection (thermal)I : for short-circuit protection (magnetic) trip unit rating80 A at 40 °C long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed [tr] long-time delay adjustment range120…400 s at 1.5 x In15 s at 6 x Ir short-time pick-up adjustment type IsdFixed [Isd] short-time pick-up adjustment range640 A short-time delay adjustment typeFixed earth-leakage protection classClass A earth-leakage protectionWith residual earth-leakage sensitity adjustment typeAdjustable 5 settings [IΔn] residual earth-leakage sensitive adjustment0.03…10 A residual earth-leakage time delay adjustment typeAdjustable 4 settings height236 mm width140 mm depth86 mm net weight2.4 kg compatibility codeNSX100 Environment overvoltage categoryClass II electrical shock protection classClass II standardsEN/IEC 60947 product certificationsMarineEACCCC IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 ambient air temperature for operation-35…70 °C ambient air temperature for storage-55…85 °C Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My Documentsprp.document.label.format pdfSize 13 MBDate 4/1/18DescriptionCompact NSX100-630 - Guide utilisateurCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 2.8 MBDate 2/27/14prp.document.label.format pdfSize 244.3 KBDate 10/24/18DescriptionYou will be redirected to the Traceparts website. Register for free or log in to your Traceparts account to download more than 15 different 2D or 3D CAD formats.prp.document.label.format zipSize 6.4 MBDate 8/4/08prp.document.label.format zipSize 6.3 MBDate 8/3/08Instruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages16
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.