Main rangeCompact product or component typeEarth leakage circuit breaker device short nameVigiCompact NSX100F device applicationSpecial application Breaking capacity codeF 36 kA 415 V AC trip unit rating100 A at 40 °C Complementary poles description4P protected poles description3t4t3t + N/2 neutral positionLeft network typeAC network frequency50/60 Hz control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront [In] rated current100 A at 40 °C [Ui] rated insulation voltage500 V AC 50/60 Hz [Uimp] rated impulse withstand voltage8 kV [Ue] rated operational voltage440 V AC 50/60 Hz breaking capacity85 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-236 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-235 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity85 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-236 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-235 kA at 440 V AC 50/60 Hz conforming to IEC 60947-2 suitability for isolationYes conforming to EN 60947-2Yes conforming to IEC 60947-2 utilisation categoryCategory A mechanical durability50000 cycles electrical durability30000 cycles 440 V In conforming to IEC 60947-250000 cycles 440 V In/2 conforming to IEC 60947-2 connection pitch35 mm instantaneous pick-up1500 A trip unit nameMicrologic 4.2 AB trip unit technologyElectronic trip unit protection functionsLSoIR protection typeL : for overload protection (long time)So : for short time short-circuit protection with fixed delayI : for instantaneous short-circuit protectionR : for earth-leakage protection long time pick-up adjustment type IrAdjustable 9 settings long time pick-up adjustment range40...100 A long time delay adjustment typeFixed [tr] long-time delay adjustment range11 s at 7.2 x Ir16 s at 6 x Ir400 s at 1.5 x Ir thermal memory20 minutes before and after tripping short-time pick-up adjustment type IsdAdjustable [Isd] short-time pick-up adjustment range1.5...10 x Ir short-time delay adjustment typeFixed [tsd] short-time delay pick-up0.02 s instantaneous pick-up adjustment type IiFixed earth-leakage protection classType A earth-leakage protectionIntegrated [I∆n] residual earth-leakage sensitive adjustment30 mA100 mA300 mA500 mA1 A3 A5 A earth leakage specific modeOFF using the IΔn rotary switch earth-leakage time delay typeAdjustable [Δt] earth-leakage time delay pick-up adjustment range0 ms60 ms150 ms500 ms1 s overvoltage categoryClass II electrical shock protection classClass II local signallingLED readyLED 90 % IrLED 105 % Ir height161 mm width140 mm depth86 mm Environment standardsIEC 60947-2NEMA AB1EN 60947-2UL 508 product certificationsCCCCBEAC IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 62262 pollution degree3 conforming to IEC 60664-1 ambient air temperature for operation-25…70 °C ambient air temperature for storage-55…85 °C net weight2.4 kg Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight2.5 kg Package 1 Height13.5 cm Package 1 width15 cm Package 1 Length19.5 cm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
User guideFormatSizeDateAdd to My Documentsprp.document.label.format pdfSize 5.7 MBDate 1/1/20DescriptionCompact NSX - Micrologic 5/6/7 - User guideInstruction sheetFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My Documents
- All Languages15
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.