Main rangeCompact product nameCompact NSX device short nameCompact NSX100F product or component typeCircuit breaker device applicationDistribution poles description2P protected poles description2t [In] rated current40 A at 40 °C [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-2500 V DC conforming to IEC 60947-2 network typeDCAC network frequency50/60 Hz suitability for isolationYes conforming to IEC 60947-2 utilisation categoryCategory A [Icu] rated ultimate short-circuit breaking capacity5 kA Icu at 660/690 V AC 50/60 Hz conforming to IEC 60947-236 kA Icu at 250 V DC 1P conforming to IEC 60947-236 kA Icu at 125 V DC 1P conforming to IEC 60947-236 kA Icu at 500 V DC 2P conforming to IEC 60947-210 kA Icu at 500/525 V AC 50/60 Hz conforming to IEC 60947-215 kA Icu at 440 V AC 50/60 Hz conforming to IEC 60947-218 kA Icu at 380/415 V AC 50/60 Hz conforming to IEC 60947-236 kA Icu at 220/240 V AC 50/60 Hz conforming to IEC 60947-2 Performance levelF 18 kA 415 V AC trip unit nameTM-D trip unit technologyThermal-magnetic control typeToggle Circuit breaker mounting modeFixed Complementary [Ui] rated insulation voltage750 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 [Ics] rated service short-circuit breaking capacity5 kA at 660/690 V AC 50/60 Hz conforming to IEC 60947-236 kA at 250 V DC conforming to IEC 60947-236 kA at 125 V DC conforming to IEC 60947-236 kA at 500 V DC conforming to IEC 60947-210 kA at 500/525 V AC 50/60 Hz conforming to IEC 60947-215 kA at 440 V AC 50/60 Hz conforming to IEC 60947-218 kA at 380/415 V AC 50/60 Hz conforming to IEC 60947-236 kA at 220/240 V AC 50/60 Hz conforming to IEC 60947-2 mechanical durability20000 cycles electrical durability10000 cycles 277 V AC 50/60 Hz In conforming to IEC 60947-220000 cycles 277 V AC 50/60 Hz In/2 conforming to IEC 60947-2 mounting supportBackplate upside connectionFront downside connectionFront connection pitch35 mm protection typefor overload protection (thermal) for short-circuit protection (magnetic) trip unit rating40 A at 40 °C Long-time pick-up adjustment type Ir (thermal protection)Fixed [Ir] long-time protection pick-up adjustment range1 In [Im] magnetic protection pick-up range500 A auxiliary contact compositionWithout local signallingPositive contact indication Width (W)70 mm Height (H)161 mm Depth (D)86 mm Environment standardsEN/IEC 60947UL 508 product certificationsEACMarineCCC pollution degree3 conforming to IEC 60947 IP degree of protectionIP40 conforming to IEC 60529 IK degree of protectionIK07 conforming to EN 50102 ambient air temperature for operation-25…70 °C ambient air temperature for storage-50…85 °C Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight1.269 kg Package 1 Height8 cm Package 1 width13 cm Package 1 Length17.5 cm Unit Type of Package 2S03 Number of Units in Package 212 Package 2 Weight15.715 kg Package 2 Height30 cm Package 2 width30 cm Package 2 Length40 cm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 71.5 MBDate 2/10/20DescriptionCatalogue Compact NSX & NSXm circuit breakers and switch disconnectors from 16 to 630A up to 690VUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages13
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.