Main rangeMasterpact device short nameMN delay unit product or component typeTime delay auxiliary device applicationControl range compatibilityMasterpact MTZ1 circuit breakerMasterpact MTZ2 circuit breakerMasterpact MTZ3 circuit breaker voltage release typeInstantaneous Complementary impulse duration200 ms time delay range0.5...3 s [Uc] control circuit voltage100...130 V AC 50/60 Hz100...130 V DC threshold tripping voltage0.35...0.7 Un open0.85 Un close supply holding power4.5 VA supply inrush power200 VA response time0.5 s0.9 s1.5 s3 s offer typeSpare part provided equipment1 instruction sheet Offer Sustainability REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 90.7 MBDate 2/13/20DescriptionMasterPact MTZ Catalog 2020 Air circuit breakers and switch disconnectorsprp.document.label.format pdfSize 10.8 MBDate 12/6/19DescriptionMasterPact MTZ Catalog numbers and spare parts 2020 Air circuit breakers and switch disconnectorsUser guideFormatSizeAdd to My Documentsprp.document.label.format pdfSize 11.4 MBDate 12/1/19DescriptionThe aim of this guide is to provide users, installers, and maintenance personnel with technical informationneeded to operate MasterPact™ MTZ1 circuit breakers and switch-disconnectors, in compliance with theIEC standards.prp.document.label.format pdfSize 12.6 MBDate 12/1/19DescriptionThe aim of this guide is to provide users, installers, and maintenance personnel with technical informationneeded to operate MasterPact MTZ2/MTZ3 circuit breakers and switch-disconnectors, in compliancewith the IEC standards.prp.document.label.format pdfSize 20.4 MBDate 3/1/19DescriptionThis document provides trained and qualified maintenance personnel with the technical information needed to perform Basic and Standard end-user preventive maintenance on Masterpact MTZ IEC circuit breakers and switch-disconnectors.prp.document.label.format pdfSize 3.8 MBDate 3/1/19DescriptionThis guide contains information on the preventive maintenance Policy recommended to ensure that masterpact MTZ devices retain the operating and technical characteristics specified during their service life.Instruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages28
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.