Main rangePowerLogic product nameCT product or component typeCurrent transformer secondary current5 A accuracy classClass 0.5 at 8 VAClass 1 at 10 VA [In] rated current500 A Complementary current transformer typeTropicalised for busbar current transformer ratio500/5 [Ith] conventional free air thermal current30 kA dynamic withstand current2.5 Ith maximum safety factor5 [Ue] rated operational voltage< 720 V AC 50/60 Hz [Ui] rated insulation voltage3 kV mounting modeInsulated locking screw mounting supportBusbar width90 mm outside: 65 mm inner: height94 mm outside: 32 mm inner: depth40 mm frame: 87 mm total: net weight0.541 kg [Uimp] rated impulse withstand voltage3 kV electrical insulation classClass B opening of bars65 x 32 sealingWith Environment standardsIEC 61869-2VDE 0414 product certificationsCE IP degree of protectionIP20 relative humidity0…95 % ambient air temperature for operation-25…60 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My DocumentsSize pdfSize 56.7 MBDate 9/17/19DescriptionPowerLogic Products Catalogue. Note that no printed catalogues are available but all necessary source files in 14 sections are available for download from the Shopping Kiosk.Size pdfSize 12.9 MBDate 9/17/19DescriptionNote that no printed catalogs are available but all necessary source files, in 14 sections, are available for download from the Shopping Kiosk.CADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My DocumentsRoHs China DeclarationFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.