Main rangePowerLogic product nameCT product or component typeCurrent transformer secondary current5 A accuracy classClass 0.5 at 8 VAClass 1 at 12 VA [In] rated current600 A Complementary current transformer typeTropicalised for busbar current transformer ratio600/5 [Ith] conventional free air thermal current36 kA dynamic withstand current2.5 Ith maximum safety factor5 [Ue] rated operational voltage< 720 V AC 50/60 Hz [Ui] rated insulation voltage3 kV mounting modeInsulated locking screw mounting supportBusbar width90 mm outside: 65 mm inner: height94 mm outside: 32 mm inner: depth40 mm frame: 87 mm total: net weight0.541 kg [Uimp] rated impulse withstand voltage3 kV electrical insulation classClass B opening of bars65 x 32 sealingWith Environment standardsVDE 0414IEC 61869-2 product certificationsCEEAC IP degree of protectionIP20 relative humidity0…95 % ambient air temperature for operation-25…60 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 12.3 MBDate 1/25/20DescriptionNote that no printed catalogs are available but all necessary source files, in 13 sections, are available for download from the Shopping Kiosk.prp.document.label.format pdfSize 9.8 MBDate 3/28/19DescriptionVigilohm Catalog English Web VersionCADFormatSizeAdd to My DocumentsCatalogue pageFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.