Main rangePowerLogic product namePowerLogic PM8000 device short namePM8214 product or component typePower meter Complementary power quality analysisconforming to EN 50160: 2010 compliance report conforming to IEEE 519: 2014 compliance report conforming to IEC 61000-4-30: class S power quality measurement up to the 63rd harmonic harmonic distortion waveform capture voltage sag and swell detection programmablity (logic and math functions) conforming to IEC 62586 power quality monitoring device applicationPower monitoringWAGES metering type of measurementCurrentVoltageFrequencyActive and reactive power totalApparent power totalPower factor totalActive and reactive power per phase, rmsApparent power per phase, rmsPower factor per phase, rms supply voltage20...60 V DC +/- 10 % network frequency50 Hz60 Hz [In] rated current5 A1 A10 A poles description3P1P + N3P + N power consumption in W17 W display typeRemote LCD display display resolution320 x 240 pixels QVGA sampling rate256 samples/cycle measurement current50…10000 mA analogue input typeVoltage (impedance 5 MOhm)Current (impedance 0.3 MOhm) measurement voltage57…400 V AC 42...69 Hz between phase and neutral100…690 V AC 42...69 Hz between phases frequency measurement range42…69 Hz number of inputs3 digital 30 V AC3 digital 60 V DC measurement accuracyCurrent +/- 0.1 %Voltage +/- 0.1 %Active energy +/- 0.2 % accuracy classClass 0.2S active energy conforming to IEC 62053-22Class 0.2 active energy conforming to ANSI C12.20Class 0.2 active power conforming to IEC 61557-12Class 0.5S reactive energy conforming to IEC 62053-24Class 0.5 power factor conforming to IEC 61557-12Class 0.2 voltage conforming to IEC 61557-12Class 0.2 current conforming to IEC 61557-12 number of outputs1 pulse information displayedVoltageCurrentFrequencyPowerEnergy consumptionHarmonic distortion communication port protocolModbus RTU at 115 kbauds - 2-wireION at 115 kbauds - 2-wireDNP3IEC 61850Modbus TCP/IPEthernet Modbus TCP/IP daisy chain at 10/100 Mbit/sRSTP 801.1d 2004 communication port supportEthernetScrew terminal block: RS485 communication network typeIPv6 (internet protocol) data recordingHarmonics logsWaveform logsTrending/forecastingEvent logsAlarm logsData logsSequence of event recordingSag and swell logsMin/max of instantaneous valuesTime stampingGPS synchronisation memory capacity512 MB web servicesCustomizable home pageFile upload/download via FTPFile upload/download via SFTPWeb serverAlarm notification by e-mailViewing of captured waveform (FTP)Viewing of captured waveform (web)HTTPS server communication serviceRSTP supportDHCPSMTP e-mail notificationNTP time synchronizationSNMPPTP time synchronization cybersecurityEnable/disable communication portsRobust security logsPort hardeningPassword protectionSyslog protocol support mounting modeClip-onFlush-mounted mounting supportDIN rail meter deviceFramework remote display provided equipmentRemote display installation categoryIII Safety ConstructionIII, 400…690 V conforming to IEC 61010-1:ed. 3III, 400…690 V conforming to EN 61010-1:ed. 3III, 347…600 V conforming to UL 61010-1:ed. 3III, 347…600 V conforming to CSA C22.2 No 61010-1:ed. 3 standardsIEC 61557-12IEC 62052-11IEC 62053-24IEC 62053-22IEEE 1588IEC 62586-2IEC 61326-1 product certificationsCECULusN998China RoHS width90.5 mm depth90.8 mm height90.5 mm product weight528 g Environment electromagnetic compatibilityElectrostatic discharge conforming to IEC 61000-4-2Radiated radio-frequency electromagnetic field immunity test conforming to IEC 61000-4-3Electrical fast transient/burst immunity test conforming to IEC 61000-4-4Surge immunity test conforming to IEC 61000-4-5Conducted RF disturbances conforming to IEC 61000-4-6Magnetic field at power frequency conforming to IEC 61000-4-8Voltage dips and interruptions immunity test conforming to IEC 61000-4-11Immunity to impulse waves conforming to IEC 61000-4-12Conducted and radiated emissions conforming to EN 55022Conducted and radiated emissions conforming to EN 55011Conducted and radiated emissions conforming to FCC part 15Conducted and radiated emissions conforming to ICES-003Conducted RF disturbances (2...150 Hz) conforming to CLC/TR 50579Surge withstand conforming to IEEE C37.90.1 IP degree of protectionIP30 conforming to IEC 60529 relative humidity5…95 % ambient air temperature for operation-25…70 °C ambient air temperature for storage-40…85 °C operating altitude3000 m Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
User guideFormatSizeAdd to My DocumentsSize pdfSize 5 MBDate 11/1/19DescriptionThe document explains the configuration and operation of the PM8000 series meters.Size pdfSize 947.6 KBDate 11/1/19DescriptionThis document describes the process to upgrade PowerLogic™ ION9000, PM8000 or ION7400 series meters to the latest firmware version. It also contains information about upgrading analog I/O option module firmware.Size pdfSize 95.2 KBDate 11/1/19DescriptionThis update provides a summary of technological advances in the Power and Energy Monitoring System offers, and the technical documentation accompanying their release.Size pdfSize 92.4 KBDate 2/1/19DescriptionWhats New in PM8000 v2.1.0 firmware. The following new features are included: Enhanced firmware upgrades, PTP time synchronization, Secure webserver (HTTPS), otherEU RoHS DeclarationFormatSizeAdd to My Documents
Software and FirmwareLanguage
Firmware - ReleasedFormatSizeAdd to My DocumentsSize zipSize 17.9 MBDate 11/22/19Files in documentzip16.8 MB942.2 KB161.9 KBDescription"This ZIP file contains the files to upgrade the PowerLogic™ PM8000 series meter to firmware v2.2.1 (V002.002.001), Meter Template, Modbus Map document, SNMP MIB, Webpages, What’s new document and other associated files. See the Upgrading Meter Firmware to v2.2.1 document for important information on performing this upgrade. Verify the checksum of the file to help ensure it was not corrupted during download using the SHA-256 File Signature for the ION9000_V002.002.001.zip file: b659d628b5e5b3fc93edb0c04403367a7bf32f54a06d6b779cb2939850b1153f. NOTE: To apply this firmware, the meter must have firmware v2.1.0. Go to schneider-electric.com and search for Upgrade devices to firmware v 2.1.0 and follow instructions on how to get and apply firmware v2.1.0."Size zipSize 14.2 MBDate 6/4/19Files in documentupg12 MBdcf863.7 KB97.7 KBzip790.9 KBmib19.9 KBzip434.8 KBDescriptionThis Release brings serveral new features and security enchancements.The security enhancements include improvement to:- Syslog server support- Designated readera nd user information in the event log- Enabling/disabling communications ports and protocols and changing port numbers- Advanced security username and password entry when using the display- New user permission setting- Increase number of users in Advanced SecurityThe new communication functionality improvements include:- DHCP- Domain name resolution (DNS)- IPv6 full supportIncreased onboard log storage capacityWebpage waveform viewerPM8000_MID_V001.004.003.upg SHA-256 checksum:7cf3f0de7ffd13aff4fa6bb6b8da167718860e883006f774860f35a5fa177877Size zipSize 16.9 MBDate 4/30/19Files in documentDescriptionFirmware version 2.1.0 for the PowerLogic™ PM8000 MID series meter adds enhanced firmware upgrade support, PTP, Secure HTTPS webserver, ION Module updates, updated support for the latest versions of EN50160, IEEE 519 and IEC 61000-4-30 power quality standards, pre- and post-event data capture for data and waveform recorders, and 0-20 mA support for the Analog I/O option module.To upgrade your meter to firmware version 2.1.0, you must use ION Setup version 3.1 or later. Please refer to the “Upgrading devices to firmware v2.1.0” technical note at https://www.se.com/ww/en/download/document/7EN72-0203/ for instructions on upgrading your meter firmware to version 2.1.0.SHA256 File signatures:c683f844c0225102d71b527c257ed5fee62603502bf150499ea65b9d139a1c95 *PM8000_MID_V002.001.000.zipSize s19Size 220.8 KBDate 3/5/19DescriptionThe 1.2.0 (V001.002.000) firmwarefor the METSEPM89M2600 Digital I/O Module is compatible with PM8000, ION7400, and ION9000 meters.SHA256 File signatures:5f88067ed29ef9d7c369410fb1785967cf1838436062a0509c6aee1ad7f0c412 *METSEPM89M2600_DIO_V001.002.000_Release.s19Size s19Size 220.8 KBDate 3/5/19DescriptionThe 1.2.0 (V001.002.000) firmware for the METSEPM89M0024 Analog I/O Module adds 0-20 mA support when used with PM8000, ION7400, or ION9000 meter firmware 2.1.0 (V002.001.000) or higher. SHA256 File signatures:77855de93e70ed9b25be9568b64eaa333c56ead286624323fbc04073cdb5626a *METSEPM89M0024_AIO_V001.002.000_Release.s19Size zipSize 28.7 MBDate 3/4/19Files in document286 KBzip28.2 MB166.7 KBDescriptionFirmware version 2.1.0 for the PowerLogic™ PM8000 series meter adds enhanced firmware upgrade support, PTP, Secure HTTPS webserver, ION Module updates, updated support for the latest versions of EN50160, IEEE 519 and IEC 61000-4-30 power quality standards, pre- and post-event data capture for data and waveform recorders, and 0-20 mA support for the Analog I/O option module.To upgrade your meter to firmware version 2.1.0, you must use ION Setup version 3.1 or later. Please refer to the “Upgrading devices to firmware v2.1.0” technical note at https://www.se.com/ww/en/download/document/7EN72-0203/ for instructions on upgrading your meter firmware to version 2.1.0.SHA256 File signatures:3cdd6e69bfa85d8b76255391270db77f504ec77385bd2dfbc3c7f6b62f31c097 *PM8000_V002.001.000.zipSize zipSize 6.1 MBDate 2/21/19Files in documentbin5.8 MBDescription"Some RD96 displays may require a two-step firmware upgrade for compatibility with the ION9000 series meter. The RD96 display firmware must be upgraded with the rmdupg_rd96s_001.000.000_patch.bin file before proceeding with the standard rmdupg_rd96_004.000.000.bin display firmware upgrade file.See the ""RD96 Display upgrade using ION9000 meter.pdf"" document and the Power Meter user manual for additional information and display firmware upgrade instructions.Note: This remote display OS firmware is not compatible with PM8000 & ION7400 meters running firmware versions 1.4.x and older.SHA256 File signatures:59c394c2c4f62cd2bb70ec2331b11ad0a03375818b83274c14ac6f8dc5644f82 *rmdupg_rd96s_001.000.000_patch.bin83c30aca20c42622d99aced8f2981ec75de63021887750a6ba7e390aded68354 *RD96 Display upgrade using ION9000 meter.pdf"Size binSize 5.6 MBDate 10/16/18DescriptionThis is OS Package version 3.2.193 for the METSEPM89RD96 remote display. It supports PowerLogic™ PM8000 and ION74000 series meters with firmware versions 1.4.x and older.See the Power Meter user manual for display firmware upgrade instructions.Note: This remote display OS Package is not compatible with meters running firmware versions 2.0.0 and newer.SHA256 File signatures:c55b87fda044cc5def860129c460d87f6c57560868315f4454306c8a49efef67 *rmdupg_rd96.003.002.193.binSize binSize 5.8 MBDate 10/16/18DescriptionThis is OS Package version 4.0.0 for the METSEPM89RD96 remote display. It supports meter firmware version 2.0.0, including the PowerLogic™ ION9000 series.See the Power Meter user manual for display firmware upgrade instructions.Note: This remote display OS Package is not compatible with PM8000 & ION7400 meters running firmware versions 1.4.x and older.SHA256 File signatures:8b0aaa760d1e705b7528ee3941e381c00cab3adc524b460a9fd04acf54a0ef37 *rmdupg_rd96_004.000.000.bin
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.